Aido completed the new furnace and AC install and returned to get the AC operational when the temperature was right for setting it up. The job was neat & tidy and very well installed.
HVAC Repair in Guelph.
Replaced failed capacitor. Capacitor charge was 21.3 mf out of 40 mf, a 5% discrepancy is allowed. Capacitor was not able to run the compressor or fan motor.
Summertime Duct Cleaning performed for a commercial client near Mini Lakes. Cleaned out the ductwork in the building to reduce pollutants in the air and keep the HVAC system working efficiently.
Summertime Water Heater Repair for a residential customer near Glenchristie with No hot water. Pressure switch problem not opening. Have to check on part availability and warranty on tank will call on Monday with cost of new pressure switch
Install Downflow Furnace.
Install (2.0T/60KBTU) Magical Comfort Series (GCVC) Downflow Furnace with 16 SEER AC & Furnace Package
Furnace Tune-Up and maintenance.
Maintenance: Gas pressures good Tested safeties, all working Cleaned flame sensor, burners and drain lines Changed furnace filter Thermostat working properly
Install Day: Replace air conditioner, Goodman 16 SEER
Maintenance Call to Clean Continental fireplace