Everton is a very knowledgeable, professional, and just a nice person!
AC Maintenance Call. Perform routine maintenance on air conditioning system.
AC Service Call. Evaluate system and check thermostat.
AC Service Call unit. Evaluate system to find drain line was clogged. Cleared drain line and unit is now cooling properly.
AC Service Call. Evaluate system to find defective thermostat. Replace thermostat with digital non programmable thermostat.
Service Cal. Pulled and clean evaporator air conditioning coils.
Service call. Clean coil and replaced refrigerant drier.
Service call. Perform coil clean and install new refrigerant drier.
Estimate for air conditioning coil cleaning. Coil cleaning will be performed on Friday.
Service call. Coils need to be cleaned. Will clean Thursday.
Service Call. Evaluate system to find coil has deteriorated and needs to be replaced. Due to age and current condition it is recommended to change entire system.
Install new air conditioning split system.
Maintenance Call. Perform routine maintenance per maintenance agreement on air conditioning system.
Maintenance Call. Perform routine maintenance per maintenance agreement on Bard air conditioning system.