The service was excellent, very efficient and good explanations of the problem
Repair toilet and fix leak in shower
Light water heater pilot for client
Water heater repair. Replace thermocouple.
Toilet repair. Replace fill valve and flapper.
No heat on free standing gas log heater. Pilot assembly replacement is a difficult time consuming repair due to fire calk that needs to be removed to replace anything in a gas log set.
Fill acid neutralizer with median
Replace UV bulb in Watts UV water disinfectant system. UV bulb should be replaced every two years. The bulb looses it power after two years.
Water heater tune-up and safety inspection. Check burner and clean assembly check base of chimney and check for proper operation.
Toilet installed by other contractor. Toil leaking and not working. Make manufacture recommended adjustments.
Oil boiler repair, replace nozzle, filter and screen sytem working fine.
Replace thermostat on gas boiler
Install nee toto toilet.
Oil boiler tune-up and safety inspection.
Install new watt UV light to kill germs and bacteria in the drinking water.