Just replaced a faulty thermostat with a Honeywell 3000 non programmable stat.
Carrier a/c tune up
Carrier furnace tuned up
Lennox furnace tune up system is ready for winter
Carrier furnace tune up system is ready for winter
A new tank was installed.
A garbage disposal was installed.
A furnace was tuned up.
Just got done installing this toilet
A new faucet and garbage disposal was installed. They will now be cleaner and more blended.
The A/C was tuned up.
We installed a brand new super awesome Faucet!
The air conditioner was tuned up and they had an SMP! Lucky them!
Maintenance check. Works perfectly.
Cleaned and Calibrated an Air Conditioner. Today's Tune-up has left this A/C running strong.