After reading the online reviews describing the excellent service customers experienced from Bayside Heating and Cooling, I was pleasently pleased and very grateful that Keving was able to come the day I called to troubleshoot my thermostat/ furnace issues. To be concise- his commitment to fixing my problem went above and beyond. His friendly, knowledgeable demeanor gave me confidence that I had truly chosen the exact company to carry out this job. After eight years of taking my heating system for granted I have now decided to begin a bi-yearly inspection by Bayside to maintain the system at optimum level. Thank you Kevin, and Bayside!
Response from Bayside Heating and Cooling:
Thank you so much for this 5-star review. We really appreciate you being a customer and helping to share the word about us. We’re here for you anytime.
Carrier gas furnace maintenancemaintenance inspection to prevent repair. Carrier high efficiency air conditioner maintenance and inspection. Refrigerant charge maintenance. Heater operation inspection and cleaning.
Performed maintenance and operational inspection for HVAC system. Inspected and clean gas furnace and outdoor air conditioner. Test system for high-efficiency operation.
Performed maintenance and operational inspection for HVAC system. Inspected and clean gas furnace and outdoor air conditioner. Tessa system for high-efficiency operation.
Air conditioning drain pan full of water in the attic. Clogged drain line. Debris inside of air handler. Remove debris. Auxiliary drain switch was preventing AC unit from coming on. Made repair and checked refrigerant charge for high efficiency.
Perform maintenance and operational inspection for HVAC system. Clean gas furnace and AC system. Outdoor coil was dirty. Also check refrigerant charge for high efficiency operation
Arrived at residential home to repair their air conditioning system. The customer had called to report that their system was freezing up. I inspected the unit and found that the air filter was dirty and restricting the airflow, which was causing the evaporator coil to freeze. I replaced the air filter and thawed the evaporator coil to resolve the issue. The system is now running optimally again for the home.
Went out to repair a customer's HVAC system that was not working properly. Upon arrival, the unit was carefully inspected, and it was determined that the condensate drain was clogged with material. The condensate drain was thoroughly cleaned to get the HVAC system back up and running. The customer was pleased with the service.
Went out to a residential home to repair their air conditioning unit. Inspected the system and found that it was not cooling due to a leak in the evaporator coil. Was able to replace the coil and change the filters. The system is now operating correctly for the customer.
Went to a residential home to provide air conditioning maintenance. The indoor unit was blowing warm air and the outdoor air conditioner was running, but not cooling. Inspected the unit and found that the system was low on refrigerant. Performed refrigerant charge maintenance for peak performance. Outdoor unit is now running efficiently.
Went out on to a residential customer who was having problems with their a/c system. Inspected the system and found that it was frozen up. Replaced the filters on the unit and increased the fan speed. The system is now repaired and operating as it should for the customer.
Went to a residential home to install a new heat pump. The old system had a refrigerant leak. Installed a high-efficiency two stage heat pump system for the customer. The new system is operating well for the customer.
Provided maintenance for an air conditioner at a residential home. Cleaned the system, replaced the filters and provided performance testing. The system is now operating as it should.
Called out to a residential home to repair their air conditioning system. When inspecting the system, found that the suction accumulator wasn't functioning correctly. The suction accumulator was replaced, and the system was restarted. It is now working properly.
Service call for high-efficiency gas furnace cutting off. Perform a system operation inspection and cleaning to determine the cause. System cutting off due to high-limit safety. Also perform humidifier maintenance.