Great attention to detail.
Our installers were excellent! Professional, friendly. Luis G, Luis M, and Daniel S. Were fantastic. During these COVID 19 times, they always had their masks on.
Replaced sewer line
Came out and made a few repairs that we had given estimates for at the home inspection. We changed the cartridge out on the lavatory in the guest bath upstairs and we changed out the Toto fill valve on the right bathroom downstairs. Everything is tested for leaks and good to go the customer paid with credit card and no follow up needed.
Customer had us out today to give estimates to replace two 50 gallon tall NG water heaters. Both heaters are leaking. Gave estimates for 6 year, 10 year and tankless options. Customer will follow up with us if they want the work done.
AC Diagnostic System:main Refrigerant Type R410A Metering Device-TXV VSAT/LSAT-47/110 SH/SC-14/8 Outdoor Entering Air Temperature -95 Filter Size(s)20x25x4 Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes: primary line has a restriction causing the inline float switch to trip and cut off the unit. Could add blow out valve and attempt to clear the primary but I strongly Recommend replacement of the system being it is 10 yrs old and a lot of money has been put into it in the past. Robin agreed to have comfort advisor quote new system. Comfort advisor scheduled tomorrow between 9-10. Staticâ€™s-RP .05 /FR .52/FS .25 /SP .12TESP: .77
Set new bathtub faucet, shower faucet and lavatory faucets. Connected all drains and water lines to all. Set new toilet and connected water to it . Turned all water on and checked for leaks . Found none and everything was working with no issues .
Follow Up Collect payment System- Master Bedroom Approx Age of System: 4yrs Refrigerant Type- R410a Metering Device- TXV SP/HP: 118/361 SLT/LLT: 53/99 VSAT/LSAT- 39/109 Superheat/Subcool-10 Outdoor Entering Air Temp- 97 Outdoor Fan FLA- .5 Compressor RLA/LRA- 6.7/31 Contactor Voltage-240/24 Capacitor Rating-35/5 Indoor Return Dry Bulb Temp- 73 Return Wet Bulb Temp- 57 Supply Temp-50 Temperature Difference- 23 Required Difference- 16-20 Blower FLA- 2.8 Filter Sizes â€“ 20x25x4 Changed Filters â€“ Y (customer supplied) Blew out drain line: N Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes Unit was operational on arrival. Checked filters. Checked operating pressures and temperatures. Checked indoor and outdoor electrical. All other components showed no visible issues at this time. Cleaned dehumidifier filter. System- Upstairs Approx Age of System: 4yrs Refrigerant Type- R410a Metering Device- TXV SP/HP: 133/379 SLT
Came out today and put the top back on the Faucet in the guest bathroom. Ran it and tested it as much as possible to ensure no leaks and we also moved it as forward as we could so she could get her hands down comfortably in the sink. Customer paid with credit card the service fee and no follow-up needed.
As Per Agreement
CU-3 threw the belts off Troubleshot and found belt on AHU 2 was broken causing the other (2) belts to come loose and fall off. Replaced (1) belt and adjusted motor. Belt was not warranty. All operational upon departure
As Per Agreement
System-upstairs Approx Age of System: 5 Refrigerant Type- R410a Metering Device- TXV SP/HP:115/314 SLT/LLT:62/95 VSAT/LSAT- 39/98 Superheat/Subcool-23/3 Outdoor Entering Air Temp-88 Outdoor Fan FLA- .7 Compressor RLA/LRA-6.7/61 Contactor Voltage-243/27 Capacitor Rating-35/4 of 35/5 Indoor Return Dry Bulb Temp-75 Return Wet Bulb Temp-65 Supply Temp- 60 Temperature Difference-15 Required Difference-16/24 Blower FLA- 1 Filter Sizes â€“ 14x20 16x25 Changed Filters â€“ N Clean Blew out drain line: N Returned tstat to original settings: Y Unit operational; prior to leaving: Y Notes-organic growth found in supply plenum and air handler, recommend an air scrubber to kill off organic growth, prevent further buildup as well as increase air quality, recommend a sanuvox uv surface light to kill off organic growth inside of system , help prevent further buildup, and help keep inside of system clean. Recommended blowout valve for both systems to allow drain line to be cleare
Arrived to the Lowe residence to replace a gfi located in master bathroom. Found water coming out of the drain pipe for the AC so I schedule a AC tech to come check it out.No need to do a follow up call.
Customer had us out today to investigate a water spot in her pantry. Found the master tub/shower directly overhead of this spot. There was an access door to the drainage and valve. Ran water and saw no signs of leaking on the drainage or valve itself. The trim plate for the valve was missing caulk and there was a small gap at the top of the plate. Caulked the trim plate and this should take care of the issue. If we need to return, we will need to cut into the ceiling below this tub to further diagnose the issue. No follow up at this time.
Return to replace ductwork Arrived on site, met with Mr Brown. Disconnected and removed old flex duct. Installed new flex to both connections underneath the home, and disposed of old flex. We do offer a Platinum Comfort Club Membership Our HVAC Comfort Club Membership is $13.95 per month per system or $167.40 yearly Benefits: Guaranteed service within 24hrs Discounted Service Charge $49 (Regular $98 afterhours $148) 20% discount on repairs Semi- Annual HVAC System Tune Ups (2 per year Cooling/Heating) Please feel free to contact our office if you would like to proceed with any of the recommendations or have any questions. Non Comfort Club $1710 Comfort Club $1368