Jeremy and James were simply excellent! In their knowledge, skill, explaining toilet plumbing details to me. Incredibly courteous and up front about cost options. I will definitely request them again for the shower and after heater installation
I really appreciated how the problem was managed by Chris. A less honorable person could have made up reasons to get more money for the service but he simply reversed the disposal blades and got it working. I appreciate that!
Nothing but positive experience. Excellent communication with analysis, recommendations, and opportunities. Quick with repair and cleanup. Also happy to see experienced plumber developing skills of the trade to their apprentice/assistant.
Is there ever a good time to have a plumbing leak? I called Bradbury and they worked quickly to address our problem. They aren't the cheapest, but I will pay for experience, professionalism and good service.
We had some issues with our furnace, that could have been very expensive. Bradbury worked with the parts supplier and found a solution that solved the problem safely and we believe reliably. They went the extra mile for us and it is appreciated.
Earnest was great and very thorough. We will be using their services from now on.
Would highly recommend.
Caleb was very professional and friendly. Would highly recommend.
Arrived to customers home for heat not coming on. Found that the vent port for the vacuum switch at the furnace is clogged and not allowing the vacuum switch to close. The port has been cleared and the furnace has been tested from the thermostat to ensure operation. While in the attic, I broke the primary drain line off at the bushing where it goes in to the plumbing stack. We are sending another tech who has the proper materials to reconnect the line in to the stack. I have instructed the customer not to turn on the A/C until the repair is made. The heat is operational at this time.
Customer had us out today to install a new water heater. We removed the old one and installed the new 40 gallon Rheem water heater. Everything went well and the unit was filled and turned on to be tested. Everything is working as it should at this time. Shane is scheduled to return Monday morning to seal around the rain collar. ***There is no follow up at this time.
System: Approx Age of System: Combustible Gas Leak Detection Pipe and fittings leak-free: no Valves and orifices leak-free: no Carbon Monoxide Testing Walk-around CO: pass 0/ppm Airside CO: pass 0/return ppm 0 supply ppm Flue gas CO: pass 27/ppm Ignition and Combustion Delayed ignition: no Flame disturbance: no Flame discoloration: no Motor Amperages and Capacitors Blower motor FLA: 7 Induced draft/combustion blower motor FLA: 1.3 Capacitor(s): pass 10/mfd Temperature Rise Rated: 1st 25-55 Actual: 1st 32 Static Pressures Blower speed/cfm: FR .31 /FS .30 /SP .11 TESP: .61 Safety Controls Primary limit test: pass Filter sizes: 20x30x1, 12x24x1 Changed filters: no customer will Scheduled next tune up date: 5/2 12-4 Notes: system was on upon arrival performed heat tune and system is operating within factory range. Unit is 12 years old so I recommend customer starts preparing for replacement due to the age. Sanubox is out and has to be
Water heater pan is full of water , didnt find any pipes leaking bringing me to the conclusion that the tank is cracked. Vacuumed al the water from the drain pan and made sure the emergency drain was clear. Will have plumbing come out tomorrow to replace water heater customer is very clear that he wants it replaced .
Came to look at the backyard grill to run gas pipe and make connections , made special work up to follow up with customer. Mentioned the comfort club he will consider. May mention when you follow up.when you call with pricing please figure out the email issue, we couldnâ€™t get the email sent on the first call.
Unjammed garbage disposal. After unjamming it i ran a lot of water and ice down to ensure whatever had jammed it up was gone.
Replaced 40 gallon water heater in attic with new 50 gallon natural gas 10 year water heater. Install new safety pan with flood stop. Install new vent through roof and sealed on roof. Heater is working properly. Noticed water in ac drain pan tried to blow it out and the units are tied together. Customer showed me a area where it was worked on before, recommend separating the lines so this isnâ€™t a constant problem for them. Estimates will be provided separate lines, we will return to clear stoppage at the next earliest appointment.
Customer had us out today to install the part for the pop up assembly for the sink in the powder bath and to look at the back yard ground water pump to replace . It will need a 50ft cord built in to it if that does exist and use a 120 plug outlet and hooks up to a 2â€ pvc pipe /will need a union . We will work on finding this pump. Also the pop up assembly wont open as quick when it is actually hooked up like itâ€™s supposed to be. We could replace it with a better one when we bring the pump if they like.
System analysis x1-Masterbedrom Inspected condenser ,unit is over amping and capacitor is weak. Also inspected furnace and heating is working great but found organic growth in the air supply plenum. For the condenser I recommended a new capacitor and compressor saver to help reduce the noise and extend the life span. For the organic growth I reccommend IAQ packages on all 3 systems. Spoke to Pam and showed her the pictures of the organic growth. Also all gas flex connectors are improperly installed, they are not leaking but I do recommend replacement of those as well.
Customer had us out today to perform the work previously quoted. I was able to repair the guest shower in the upstairs bathroom with the new positemp cartridge but was unable to change the whole home shutoff valve. After opening the wall to expose the pipe and valve I found the inlet pipe to be 1â€ (crimp ring) pex while the outlet to be 1â€ copper. I donâ€™t have a set of pex crimpers on my truck so a follow up will be needed. There wonâ€™t be an additional service fee on the follow up visit. Everything is working as intended at this time.
Front system not cooling. Found that the blower wheel had fallen apart, and the motor has burnt up. Also found that motor was still receiving a signal to run. Checked low voltage wires and determined that the system was idle yet board was still sending run signal to blower indicating a failed control board. Provided estimate to replace blower motor, wheel, capacitor and control board under manufacturers parts warranty, does not cover labor. Office will call back once we get parts on had to schedule repair visit. Client chose to sign up for club membership at this time.
System: downstairs Approx Age of System: Combustible Gas Leak Detection Pipe and fittings leak-free: yes Valves and orifices leak-free: yes Carbon Monoxide Testing Walk-around CO: pass/0 ppm Airside CO: pass/return 0 ppm supply 0 ppm Flue gas CO: pass or fail/12 ppm Ignition and Combustion Delayed ignition: no Flame disturbance: no Flame discoloration: no Motor Amperages and Capacitors Blower motor FLA: 2.87 Induced draft/combustion blower motor FLA: 1.29 Capacitor(s): n/a Temperature Rise Rated: 1st 30-60 /2nd 40-70 Actual: 1st 53 /2nd 58 Static Pressures Blower speed/cfm: RP 0.04/0.04 /FR 0.08 /FS 0.17 /SP 0.06 TESP: Safety Controls Primary limit test: pass Filter sizes: 20x25x4 Changed filters: no. They were just changed in September and they are still clean. Scheduled next tune up date: Notes: Mr. Greene showed me the duct that had the proper clearance from the flue vent but the inspector asked that we pull it back a bit more. I t
System: Approx. Age of System: 7yrs Combustible Gas Leak Detection Pipe and fittings leak-free: yes Valves and orifices leak-free: yes Carbon Monoxide Testing Walk-around CO: pass/ppm 0 Airside CO: pass/return ppm 0 supply ppm 0 Flue gas CO: pass/ppm 16 Ignition and Combustion Delayed ignition: no Flame disturbance: no Flame discoloration: no Motor Amperages and Capacitors Blower motor FLA: 4.1 Induced draft/combustion blower motor FLA: 1.0 Capacitor(s): fail/4.01mfd Temperature Rise Rated: 1st 30-60 Actual: 1st 53 Static Pressures Blower speed/cfm: RP .60 /FR .60 /FS .38 /SP .10. TESP: .98 Safety Controls Primary limit test: pass Filter sizes: 12x36x1 Changed filters: No Notes: Unit was operational on arrival. Checked filters. Checked ignition and combustion. Checked safety controls and static pressure. Filter should be cleaned. Ms. Gina said she will clean filter. Unit has no gas sediment trap. Blower motor is bad rated for 10mfd.
Check slow drain on disposal. Found stiff gasket and disposal is rusted. Recommend replacing garbage disposal. Replace garbage disposal and tested.
Came out for whole home plumbing inspection. Found multiple issues and gave estimates for repairs. Replaced outdoor hose bib and scheduled master bath shower valve replacement for Thursday Dec. 12 at 8-10. Tested hose bib for leaks and operation. Everything is operating as it should.