Highly professional and proficient
Furnace tune up
Cleared out drain
Servicing a Lennox furnace that isn't working. Replacing faulty gas valve.
Water source heat pump in a condo was. Not working. Customer called multiple other companies and no one would come and fix it. I showed up and found the issue and gave customer mutiple options. We are now installing a new quieter more efficient option. Customer is very happy.
Completed furnace tune up on a Lennox furnace. Informed customer of expired carbon monoxide detectors. She was very happy to know that she needed new ones. Furnace checked out good.
Had a no cool on this customers system. Added a sealant to seal the leak and charged the system back up. Gave. Customers options on new system and signed them up on the club. To save them 15% on repairs done. System is working good now. Customer is very happy we could take care of them on a holiday weekend.
Furnace and ac inspection
Tuneup on a Heil furnace.
Installation of new Goodman 80% furnace
Trane furnace inspection