got screwed for alot of money...had Brian over and he explained what the other expensive plumber would NOT tell me that could've saved me alot of $$$$$ ! I'm an old Cabrillo customer...I'm back to stay...if you want your problem solved call Cabrillo!
Thanks, Frank, for the quick, courteous, and very professional service call today.
Clean, polite and expert service. Highly recommended.
I've used Cabrillo for over 15 years, they are quick, reliable and reasonable! Highly recommended..
Patrick installed a new kitchen faucet for me, and his work was excellent. I'll definitely call Cabrillo Plumbing and ask for Patrick again when I need some other plumbing service. Thanks!
Not the first time using Cabrillo, and not the last.
Brian was top notch in every way
My furnace and hot water heater are in the attic. Service personnel must carry an 8-foot ladder through my house, up a flight of stairs through my bedroom and enter a tiny trap door in my bathroom ceiling in order to access the equipment. Tony and Brian were fantastic, ever so careful of my flooring and furniture. And not at all dismayed by the difficulty of access.
HVAC technician installed new section of 12" duct work in crawlspace. Install new insulation for furnace supply and return air plenums. Install new Selkirk double wall vent pipe for furnace.
Plumber installed new continuous waste, P trap and sink strainers for kitchen sink.
Snaked a stoppage in a bathtub and replaced a shower head.
Plumber installed a new Insinkerator 3/4 horse power garbage disposal.
HVAC technician performed annual maintenance on Trane furnace.
Plumber removed drain blockages in bathtub and lavatory sink drains.
Plumber installed new Bradford White 40 gallon water heater with a new safety pan.
Plumber removed and reset toilet to locate source of reoccurring toilet stoppages.
Plumber cleared stoppage for shower stall drain.
HVAC technician installed new igniter for Trane furnace. Also performed annual maintenance on furnace.
Plumber cleared stoppage in light well.
Plumber repaired old 3 handle tub and shower faucet.
Carrier furnace not working. Found draft switch tripped. Filter plugged. Tested draft and unit operations. Everything ok at this time.
Plumber cleared blockage in lavatory sink drain line.
Maintenance on two furnaces and two water heaters. Replaced filters, vacuumed and tested. Everything ok at this time.