Chris is just so wonderful! He always explains things to me so that I can understand. He is efficient, kind, warm, and very trusting. I can not say enough about how wonderful he is. Thank you so very much.
I called in on Sunday of Memorial Day weekend and the phone was answered by a "live" person - she gave me an indication of when they might call me back - the owner called me Monday evening and said he would send a guy the next day - they would call me 1/2 hour beforehand - all smooth and just a perfect experience!
Preventive maintenance on a Burnham K2 high-efficiency natural gas boiler and indirect water heater.
Free estimate on an oil to natural gas conversion of a boiler and indirect water heater.
Preventive maintenance on a Viessmann condensing boiler natural gas.
Oil to natural gas conversion of a high-efficiency condensing Viessmann boiler and indirect water heater. Run gas line to stove and boiler. Removal of oil tank.
Run natural gas line for future oil to gas conversion of a high-efficiency boiler and indirect hot water heater.
Heating service call. Preventive maintenance on a natural gas condensing Burnham K2 boiler.
Free oil to Natural gas conversion estimate on an installation of a high-efficiency boiler/furnace with hot water heater and removal of oil tank.
Air conditioning service call. No cold air blowing from the vents. Replaced capacitor on a lux air air-conditioning system condenser.
Home inspector reported issue with condensate drain. Replace section of condensate to adequate standard of inspection.
Customer states unit had funny smell when on. Clean evaporator coil on Carrier AC System. Customers states house smells fresh again.
Run gas line for oil to gas conversion.
Free oil to natural gas conversion estimate for a high efficiency Viessmann condensing boiler and indirect hot water heater. Free estimate to remove Roth oil tanks.
Preventive maintenance on an oil fired Williamson hot water boiler. Clean and service oil burner.
Customer states no cold air blowing from wall mount ductless unit. Found to be bad capacitor. Replace capacitor on Goodman mini split system.