Very good and fast repair.
Comfort Control has been servicing my HVAC for over 15 years and have generally done a good job. I love how they provide text alerts notifying you that the technician is in route and who it is. My only complaint is the constant up selling. They just installed a new HVAC system and now I’m being told the duct work needs to have new insulation wrap. I just had new insulation blown in 3 years ago by a different company and now I’m being told I should have more insulation blown in. When they installed my previous system 9 years ago after that it was one thing after another that they said I should have done to fix the things that were not done or done incorrectly. Despite these complaints I stick with them because of their prompt and overall good service.
Excellent knowledgeable tech
I had a concern with how low to the ground the AC unit was installed. Took a little time but they came out today to raise the unit a few inches and I’m happy that it’s off the ground.
Heating maintenance in Alpharetta. Tested operation of 2 furnaces. All components tested within normal manufacturing spec. Upstairs needs ultraviolet light bulb replaced, downstairs needs one installed, also recommend surge protection for systems. Water heater has failed and needs to be replace. Homeowner has chosen to replace water heater with State 50 Gallon Gas water heater with new PRV and new valves. Homeowner is paid in full
Heating tune up in Alpharetta. Tested operation of 1 furnace. All components tested within normal manufacturing spec. System needs duct cleaning, blower cleaning, and water safety. System heating at this time. Could not get in contact with landlord for payment
Heating tune up in Alpharetta. Tested operation of 1 furnace. System over heating and shutting down, flame safety is worn along with ignition. System has no water safety, ducts and indoor coil in very rough condition, blower wheel dirty. Due to age and condition of system replacement is highly recommended over repair.
Heating tune up Alpharetta Georgia. Tested operation of 2 systems. All components tested within normal manufacturing spec. Discovered upstairs gas line without sediment trap, and with no drain line water safeties which is especially necessary with a water producing furnace in the attic. Downstairs furnace has dirty blower wheel. Systems would greatly benefit from ultraviolet light systems to combat organic and viral growth in systems and throughout the home. Systems heating at this time. Homeowner selling and not interested in repairs
Free consultation Alpharetta Georgia 30005 new hvac system furnace AC install
HVAC inspection in Alpharetta. Tested operation of 1 system upstairs. Discovered system 22 years old with failed thermostat, burnt main electrical switch, stressed compressor and outdoor fan motor, weak controller, dirty ducts, no drain line water safety. Due to high repair cost and age of system replacement is highly recommended.
Service call in Alpharetta. Replace upstairs Amana gas furnace low/high fire air pressure sensor. Check and test, system operating at this time.
No heating in Alpharetta. Find upstairs gas furnace low/high fire pressure sensor fail intermittently. Need order and come back to replace. Part will not be in til Thursday noon.
Heating maintenance in Alpharetta Georgia. Tested operation of 2 systems. Discovered upstairs blower motor controller weak and outside of manufacturing spec. Both systems have no secondary water safety. Both systems would greatly benefit from ultraviolet light systems to combat organic and viral growth in systems and throughout the home. Both systems would also greatly benefit from compressor saver hard start kits to reduce stress on compressor and reduce energy consumption on start up which will extend the life of the systems. Systems heating at this time
Heating maintenance in Alpharetta. Tested operation of one system. All components tested with a normal normal Manufacturing specs. Recommend ultraviolet light system to combat mold in viral growth in the system and throughout the home. Recommend surge protection for indoor unit and more efficient air cleaner. System heating at this time.
Heating repair in Alpharetta. Discovered pressure port clogged on furnace. Cleaned port system heating at this time. System has no drain line water safety, a duct is completely Detached in the attic, filter is very restrictive and system at home could benefit from an ultraviolet light system to combat mold in viral growth in the system and throughout the home. System could also benefit from a duct cleaning. Sign homeowner up for maintenance membership
No heat Alpharetta. Completed diagnostic. Found gas valve failed. Power going to it but no activating. Changed gas valve. Clicked open but no gas. Gas has been turned off. Need gas company out to turn on gas.
Heatpump diagnosis in Alpharetta, Georgia. Customer reports that lobby.zone wonâ€™t go above 55 degrees. Tested system and the only issue I found was that the outdoor fan capacitor was slightly weak. The duct run to the lobby is very long and will cause a velocity/ temperature loss. Dampers are operating properly. Refrigerant levels are good.
Furnace not heating in Alpharetta, Georgia. Found igniter to be bad. Replaced igniter under warranty. Tested other mechanical and electrical components, found no other mechanical concerns. System does not have water safety, recommend adding on to help protect crawl space from potential flooding in the event that there is a drainage issue with the hvac system. Recommend surge protection to protect equipment from power surges. System is heating at this time.
Heating issues in Alpharetta Georgia. Bad ignition. Replaced hot surface ignition and system is now heating properly.