Tran was very thorough and explained the options for what we needed on our HVAC system. Very pleasant and knowledgeable technician.
Ta was very knowledgeable about HVAC theory and equipment. He was very straight forward in his investigation and identified the problem quickly after troubleshooting.
Friendly staff and professional service.
1 system cool pm. Cleaned outdoor coil and checked all components. All capacitors have good readings, systems has 2 forms of water safety, system would greatly benefit from a compressor saver hard start kit and and ultraviolet germicidal light system to combat virus and bacterial growth through the air in the home. System cooling at this time
2 system cool pm. Cleaned outdoor u it and checked all components. Main floor system Outdoor capacitor is weak and out of manufacturing spec. Both systems could benefit from a compressor saver hard start. Upstairs system desperately needs a duct cleaning as the ducts are very dirty and the blower wheel is starting to get dirty which will cause it to be unbalanced and cause damage to the motor. Both systems are cooling normal at this time. Replaced main level outdoor dual capacitor
2 system cool pm. 43* outside. Cleaned outdoor coils and checked all components. All components have good readings within manufacturing spec. Upstairs system does not have a secondary water safety. Neither system has compressor saver hard start kits and both systems need duct cleanings. Added overflow protection water safety upstairs. Systems operation normal at this time
Customer changed thermostat and wired wrong which fried the transformer for the zone board. Replaced transformer and system started working again. Damage has been done to old zone board. If system stops working again need to return with 2h2c zone board
Rebuilt entire drain line for furnace and evap coil with new pvc. Used primer and glue on every joint
Replaced all 4 ultraviolet bulbs. New bulbs good for 2 years
Completed diagnostic found bad water switch replaced with inline float switch.
4 systems cool pm. Cleanest outdoor coils and checked all components. All capacitors are good. All contacts in good shape. Compressor saver hard starts installed last year. All indoor capacitors are good. Changed all filters which homeowner supplied. Tested all cooling operation and all system cooling normal at this time. All 4 ultraviolet bulbs are over 2 years old and need to be replaced
Pvc fitting for drain was flexed into place from original install came apart and was leaking water out when ac was running. Water damage from attic al the way to basement. Need to return to rebuild entire drain line
Complete 2 system a/c repair and preventative maintenance check. Cleaned outdoor coils and check all components. The Upstairs system has a weak dual capacitor and is causing stress on the motors. Need to replace the capacitor and add compressor savers to both systems to reduce stress on compressors, extend the life of systems and capacitors. The Upstairs system also does not have a secondary watery safety for the drain line. Need to install one to help prevent flooding in attic due to common drain line clogs. Replace the upstairs dual capacitor.
Complete 2 system A/C repair and preventative maintenance check. Cleaned outdoor coils and checked all components. Outdoor starters are weak but all other electrical in good condition. The Upstairs system has no secondary water safety. Both media filters are good. Changed 1" filter in the basement. Changed both starters. Systems cooling at this time
Complete 3 system a/c repair and preventative maintenance check. All components tested in normal ranges. The upstairs system was not cooling due to the drain line for 90% furnace came loose and filled up pan preventing cooling from coming on. Fixed drain lines and glued them but the is no secondary water safety on the system to protect against common drain line clogs. Mold is growing on a humidifier and inside plenum. Need duct cleaning and ultraviolet system to combat mold growth None of the systems have compressor savers on them. Blower cap in the basement system is still weak. Homeowners just want to wait until the system dies. They do not want secondary water safeties
Complete 1 system A/C repair and preventative maintenance check. Change filter customer provided. Check drain and operations. Find system operating within manufacturer spec. Suggest hard start kit for compressor. Find molded plenum, suggest pureAireX air purifier system to help kill mold and improve air quality.
Changed both filters 16x25x1. Complete 2 system a/c repair and preventative maintenance check both systems are running properly at this time. Found the contactor with pitting and charting on downstairs, outdoor system. I found no secondary water safety on both systems. Found that both outdoor systems do not have compressor saver kits. Tested all electrical and mechanical components and all readings are nominal.
Complete 1 system a/c repair and preventative maintenance check. Change filter, check operations and clean ac coil. Find a 10-year-old cooling system operating within manufacturer spec. Need a hard start kit and suggest surge protection. Suggest additional inline water protection. Suggest an air purifier system. System operating at this time.