Reece is very professional and let me know the status of my units as well as gave me alternatives as far as replacing my systems.
Reset thermostat and system is operating normal at this time. Inducer motor is worn and noisy, recommend replacing motor.
2 furnace pm check complete. Changed filters. Tested mechanical and electrical components. Found main level furnace operating with a weak blower motor controller. Recommend repair. Systems are heating at this time. Renew 2 system cci plan. Insulation level is low, recommend blowing more in.
Warranty call. O wire was misplaced causing system to stay in cooling mode. Rewired it to proper place, tested heating and cooling mode and system is operating properly. Put backplate behind wireless tstat.
I found the system with a bad ignition module. The gas valve may be damaged also but we will not know for sure until the ignition module is changed. I couldnt find the part. You must be a authorized dealer. I gave a price to replace the system for 4900 without Apco and 5350 with Apco. I collected the 79 for today.
Warranty. Water leak at the pvc flue pipe. Removed, primer and glued joint. No leak present at this time
2 system furnace prepaid pm. Replaced both filters, could not test upstair system do to remodel of kitchen and no gas to furnace. Downstair system heating normal. Suggest to have a combustion calibration for main floor furnace for max efficiency. Overall system is heating normal. Will do furnace maintenance upstair next visit
Performed 3 System Maintenance. Installed 3 Nest Pro Tstats. After inspection I informed the homeowner that the entire basement system is outdated and out of code. The MainFloor and Upstairs furnaces were also older and not in the best of condition. An existing humidifier from original install needs to be removed or updated. The humidifier is currently not operational. The homeowner would like the office to call Monday to schedule a consultation to further discuss these matters.
2 furnace pm check complete. Did not change main level filter. Main level mechanical and electrical components in good shape. Main level furnace has good combustion readings. Main level flue pipe is no longer up to code, it is single wall and should be double wall. Did not change upstairs filter. Upstairs furnace has worn ignition system with silica dust build up, recommend changing next year. Dusted out furnace cabinets. Insulation levels are low, recommend adding more insulation. Systems heating at this time.
2 system furnace prepaid.replaced filter, checked electrical and safety switches all ok at this. Need to change uv bulbs, owner will wait till spring tim. Both system heating normal
Complete heating pm check. Find furnace operation with worn flame safety and need to keep check on flame safety. Find minor ware on ignition. Find burner dirty and clean burner for customer. Replace filter. Check safety and operation. System operating at this time. Find mold at evaporator supply plenum. Need to sensitize and clean plenum for $350 or install apco air purifier to kill mold and prevent molds.
2 system furnace renewal. Replaced filter, checked electrical and safety switches all ok at this time. Upstair heating normal, downstair needs a combustion calibration. Calibrated main floor system and it is now heating at max efficiency.
Complete 2 heating tune up. Change both filter. Check safety and operation. Find both heating system operating normal. Do not see any concern at this time.
We installed a full system for the main floor and added the basement to it by zoning it. The system has passed all leak tests and has been uprgraded to code compliance. The price is $10000. The system came with a 10 year parts and warranty and a 1 year no breakdown gauranteed.
Complete 2 heating pm check. Check safety and operation. Change filter. Find both heating operating normal this time.
Complete 2 heating pm check. Change both system filter. Check safety and operation. Find upstairs system operating normal. Find main system operating with high co level and 77% efficiency. Complete combustion calibration HM5A to help reduce co level ad improve efficiency. System operating at normal at this time.