Very good and fast repair.
Comfort Control has been servicing my HVAC for over 15 years and have generally done a good job. I love how they provide text alerts notifying you that the technician is in route and who it is. My only complaint is the constant up selling. They just installed a new HVAC system and now I’m being told the duct work needs to have new insulation wrap. I just had new insulation blown in 3 years ago by a different company and now I’m being told I should have more insulation blown in. When they installed my previous system 9 years ago after that it was one thing after another that they said I should have done to fix the things that were not done or done incorrectly. Despite these complaints I stick with them because of their prompt and overall good service.
Excellent knowledgeable tech
I had a concern with how low to the ground the AC unit was installed. Took a little time but they came out today to raise the unit a few inches and I’m happy that it’s off the ground.
Jordan Roper was very professional and a pleasure to work with. He wore a mask and was careful about social distancing. He was friendly and explained everything he did. Great job!
As always you did an awesome job. :)
No heat upstairs in Alpharetta. Check and find Amana gas furnace flame sensor fail and system calibration off. Replace sensor and complete combustion calibration service to help temperature, improve efficiency and balance blower assembly. System operating at this time. Suggest surge protection and additional water protection in attic. Suggest air purifier system.
Water heater not working in Alpharetta, Georgia. Right water heater pilot went out. Relit pilot light. Found slight drip inside water heater dripping onto burner area. This means thereâ€™s a small leak in the tank. Recommend replacement of water heater. Customer is replacing water heater. Collected $500 deposit so total after install is $975.
Heating maintenance in Alpharetta. Tested operation of 1 heat pump system. All components tested within normal manufacturing spec. Thermostats are functional but outdated and inefficient along with main level stat hanging by the wires. Recommend upgrading both thermostats. System heating normal at this time
Free consultation in Alpharetta Georgia 30005 hvac estimate
Sign 3 comfort control maintenance plan and complete heating maintenance in Alpharetta. Find upstairs 17 year old Trane gas furnace operating with rusted evaporator coil, worn ignition and flame sensor, missing in-line water protection. Find main level 17 year old Trane gas furnace operating with worn ignition and flame sensor, under-fire furnace with high CO level. System dirty and no water protection. Find basement Payne 12 year old Airhandler leaking water due to clogged drain. Clear drain for customer and change filter. System operating at this time. Suggest in-line water protection. Customer want to wait on repairs. All 3 system operating at this time. Give customer estimates.
Sign up 2 comfort control maintenance plan and complete 2 heating maintenance in Alpharetta. Find 2 Amana gas furnace in attic. Change upstairs filter, check safety and operations. Find 2 7 year old furnace operating with weak flame sensor and under-fire furnace. Find duct works undersize and not R-8 rated. Complete repair on furnace, replace flame sensor and combustion calibration service. Suggest surge protection, suggest in-line water protection and air purifier.
One system heat maintenance in Alpharetta. Arrived on site, checked upstairs unit. Main level was blocked off at the time of visit. Changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found system with dirty blower assembly, blower motor starting to leak oil due to stress put on it from the dirt on the assembly as well as a low reading capacitor, gas line not run properly (needs Drip-t). Combustion analysis states that combustion is too oxygenated and should be adjusted. Recommend equipment be replaced as apposed to repair. Unit is operating at this time.
HVAC in Alpharetta. Dropped filters off by garage door between house and plant due to Highwinds did not want it blowing away.
Heating repair in Alpharetta. Discovered system locked out on pressure switch. Cleaned port and furnace heating normally. Tested multiple times and system heating without issue. Homeowner signed up for maintenance membership. Performed maintenance on furnace. Changed apco ultraviolet light lamp. System operation normal at this time
Heating repair in Alpharetta. Discovered furnace power switch off. Turn the power switch on and system started heating. Checked operation and all components. Discovered weak blower motor controller but all other components testing within normal manufacturing specs. System is eating at the Stone
Heating maintenance in Alpharetta. Tested operation of 2 furnaces. All components tested within normal manufacturing spec. Upstairs has no drain line water safety. Downstairs system ductwork dirty and needs a cleaning. System and home would greatly benefit from ultraviolet light systems to combat organic and viral growth in the system and throughout the home. Both systems heating at this time
Heating maintenance in Alpharetta. Tested operation of 1 furnace. All components tested within normal manufacturing spec. System and home would greatly benefit from an ultraviolet light system to combat organic and viral growth in the system and throughout the home. System heating at this time
Ac repair in Alpharetta. Discovered upstairs system low on charge. Homeowner chose to top system off. Charged system. System cooling at this time. System really need a maintenance
HVAC inspection in Alpharetta. Tested operation of 2 HVAC systems. Ac portion of both systems operation is normal other than the upstairs ac is missing service caps for refrigerant service ports and both ac systems need maintenance as the outdoor coils are dirty. Discovered upstairs furnace with dirty blower wheel, weak and leaking blower motor controller and dirty ductwork. Main level furnace which is located in the basement also has a dirty blower wheel, weak blower motor controller and dirty ductwork, but also has a very worn ignition system. Both upstairs and main level furnace are 19 years old. Typical life span is 10-15 years. Due to age and condition of furnaces, replacement is highly recommended.
Heating maintenance in Alpharetta. Tested operation of 2 furnaces. Downstairs system producing high amounts of carbon monoxide, combustion chamber is rusted, flame safety has heavy signs of wear as well as the ignition system, system could use a duct cleaning. Upstairs furnace has no drain line water safety and gas line is not up to code and system could use a duct cleaning as well. Both systems are at end of expected life and replace of downstairs system should be considered. Both systems heating at this time