Found the problem in no time and back running. good job Reese
Good services and price.
Found clooged inducer port where barometric tubing connects inducer motor to pressure switch. Cleared port and system is heating at this time.
Complete 4 heating tune up. Replace filter, check system safety and operation. Find system system #1 operating with low charge but did not detect leak at this time. Find compressor capacitor weak. Find fan motor starting to make noise and will need to keep check. Find system #2 operating with burnt and damage contactor and gas line not up to code. Find system #3 operating with worn and weak flame sensor. System #4 have worn and weak flame sensor and ignition starting to turn white due to ware. System #1 replace capacitor and 2 lbs of R410A System #2 replace contactor System #3 replace flame sensor System #4 replace flame sensor
3 system furnace renewal. Upstair New system is prepaid and early bird renewal for main floor and basement system. Upstair and basement system heating normal. Replaced main floor ignition and flame safety sensor. Main floor needs a combustion calibration, owner will wait till this fall time to have it done. All system is heating normal
2 furnace pm check complete. Changed filters. Furnace for left side of house: Tested combustion and found low carbon monoxide levels (23 ppm) , slightly high oxygen levels (10.1%) with the furnace operating at 79.6 % efficiency. Furnace has a worn flame safety and a worn ignition system, they are still functioning, but either could fail at any time. Recommend repair. Furnace for right side of house: Tested combustion and found low carbon monoxide levels (30 ppm), slightly high oxygen levels (10.2%) with the furnace operating at 82% efficiency. This system also has a worn ignition system and flame safety system. Recommend repair. Systems are heating at this time.
2 furnace maintenance check complete. Changed filters customer provided. Tested mechanical and electrical components, all in good shape. Recommend APCO air purifiers to help keep evaporator coils clean and to kill bacteria, germs, and viruses for improved air quality. Recommend surge protection to protect furnaces from power surges. Systems are heating normally at this time.
No heat upstairs. Check and find heating system fail due to burnt power switch, replace power switch and system still did not operate. Test and find furnace control board burnt and ignition damage. Replace both control board and ignition under warranty, but no labor. System operating at this time. Suggest surge protector to help protect equipment electrical.
Complete 2 heating pm check. Change both filter, check safety and operation. Find both heating system operating normal. Find upstairs flame safety weak, customer want to keep check on flame safety and wait to replace. Find downstairs drain pan have water from 90% furnace due to frozen drain line in winter. System wire to shut off AC and not heat. Customer want to keep it that way. Told customer we can rerun drain to main house drain but not code.
No heat. Find fan stand on continues due to faulty fan control. Give customer estimate to repair but customer decline. Need to call and collect for diagnostic fee. Need to get customer email.
Completed maintenance on 2 systems. Replaced dirty air cleaner filter. Checked all electrical, mechanical and safety components. Both units are operating normally at this time.
Something wrong with thermostat. Found a message on the eco bee thermostst with auxiliary heating longer than normal. Lower the auxiliary heating to 40 degree instead of 70 degree. System heating normal
No heat upstairs. Check and find upstairs thermostat not program properly. Reset tstat and system operating normally. Complete 2 heating pm check. Find downstairs heating system operating with worn ignition and weak flame safety. Find humidifier panel molded. Replace W/P #10 and clean mold for the customer. Customer wants to wait to repair heating system or replace heating system. Both heating system operating at this time.
Heat pump repair. Diagnose and perform annual heating maintenance on Carrier Heating System. Inspect heat exchanger for deterioration. Check fan switch. Clean and adjust pilot assembly on 10 year old HVAC system). Replace air filters. Furnace maintenance complete which will help lower heating cost for residential customer. Furnace system is now ready for the winter weather.
Found bad circuit board on 23 year old furnace. Recommend new system customer wants to know about circuit board in the morning.
Found weak flame safety and weak blower motor controller. Replaced both parts and system is heating at this time.
2 furnace pm check complete. Changed upstairs filter. Didn't change main level filter. Customer's daughter's room is cold in the winter and hot in the summer. Checked ductwork and it is the longest duct run from the system, branching off of another duct. The duct also has a lower insulation value. All current ductwork is r5.8, which is not optimal. Recommend ductwork renovation to increase comfort and efficiency of upstairs system. We can do a full ductwork renovation for $1750 or we can rerun a new duct to daughter's room for $500. Down stairs system is operating with worn ignition system and weak flame safety, recommend replacing those parts. Systems are heating at this time.