Reece was super profesional and found the problem with my furnace right away. I felt comfortable with him being in my home.
All the reps / tech that was at my house installing 2 AC units were very professional
Reece was very helpful and got my system repaired and running. He was patient with me and explained well as he answered my questions.
Always timely, polite, and knowledgeable
Garrett was great. Really enjoyed his expertise, courtesy, and cleanliness.
Dehumidifier is low on refrigerant and needs to be replaced. Customer wants to think over options.
No heat in Duluth, arrived on site to new install found gas cock off, turned gas on to system and tested heat cycle. Unit is operating normally at this time
Heating maintenance one system Duluth. Arrived on site, checked electrical connections,amp draw and capacitance. Checked ignition system and filter. No issues present at this time. Installed surge protector for furnace.
Casey had reported crack inside furnace on backplate area connected to heat exchanger. Confirmed damage. Blower wheel is very dirty and ductwork is too. Recommend replacement of furnace and duct cleaning.will apply diagnostic fee towards installation
Ac service in Duluth. Discovered condensate pump safety had system shut off. Shook pump and realigned top with base and system came on. Added bleach to lime to kill mildew build up in pump. System cooling at this time
2 Ac coil replacements in Norcross
Ac service Duluth. Completed diagnostic. Found system frozen on arrival. System is leaking r22 Freon. Customer had it filled 2 months ago and has already leaked out to the point of freezing. System 17 years old. Ac and coil need to be replaced. Having jim come out to give quote.
Ac service Duluth. Completed diagnostic. Found bad condensate pump. Replaced pump. Required pump. Tested pump. System cooling properly at this time.
Thermostat failure in Duluth. Found intermittent Icomfort thermostat failure on main level system. Will need to replace under warranty.
Warranty no cool Duluth Arrived on site, found upstairs system not cooling, outdoor unit throwing code for open start sequence. Checked and found bad capacitor. Changed capacitor and tested system, unit is operating normally at this time
No cool main level air conditioning system in Duluth. Find Trane system tripped breaker due to stress compressor and weak starter. Find 26 year old Trane system with burnt and damage wire and connector. Repair wire for customer, replace starter kit and capacitor. Find upstairs 14 year Trane system with weak starter kit and damage line wire and burnt capacitor wire. Replace starter kit and repair burnt wire for customer. Find office 3 year old Amana system operating within manufacturer spec. Replace media filter 16x25x5 and APCO UV bulb. Clean both Tran electric air cleaner. All 3 system operating at this time. Sign 3 CCI plan and complete 3 cooling pm check. Customer have $50 off discount
No cool in Duluth for Amana system. Find air conditioning system fail due to bad capacitor. Replace capacitor under manufacturer warranty. Find system operating without hard start kit, suggest to install. Find main electrical switch worn/pitted. Find system in attic, system operating with low insulation in attic and R4 ducts system with poor runs. Air conditioning system operating at this time. Customer want to wait til spring visit to replace main electrical switch and hard start kit.
3 system heat maintenance in Duluth. Tested all components and combustion on 3 Lennox furnaces. All components and combustion tested within normal manufacturing spec. Changed filters. Recommend drain line water safety for master system and ultraviolet systems for all 3 units to maintain indoor air health and combat mold and virus growth. All systems heating normal at this time
Complete tune up special on Rheem air conditioning system in Duluth. Check and find ac unit not operating due to tripped breaker. Reset breaker and ac unit operating at this time. Find wrong size starter kit and capacitor getting week. Need to replace to help system run smoother. Give customer estimate to repair. Change 2 16x25x1 filter for customer.