Garrett was very nice and provided great service!
Vu got out here quickly and explained everything in detail. He took the time to answer all of our questions and he didn’t feel like a pushy salesman. Great customer service!
Vu Tran was just awesome! From the minute he arrived, he was a wealth of information. He made sure to explain the “why” of everything he did or recommended. He was great - start to finish!
Reece was super profesional and found the problem with my furnace right away. I felt comfortable with him being in my home.
All the reps / tech that was at my house installing 2 AC units were very professional
No heat main level in Duluth. Check and find d error code for second stage lock out due to dirty dirty and air flow restrictions. Find filter dirty and replace filter customer provided. Find Lennox gas furnace not operating with in manufacturer spec due to in-complete combustion and under under fire furnace. Need combustion calibration service. Find air distribution plenum have bio growth and need air purifier system to help kill mold and keep system clean. Suggest comfort control maintenance plan. Customer want to look over their options. Give customer estimates. Furnace operating at this time.
Free consultation for hvac system Duluth Georgia 30096
No heat in Duluth. Check and find gas 17 year old gas furnace lock out I safety. Test and find duct system undersize for equipment, high static pressure, poor supply and return plenum and air distribution plenum molded. Find inducer assembly locking up and high temperature. Find ignition and flame sensor worn and weak. High CO level due to incomplete combustion. Pressure switch also worn and not closing properly, intermittent loose connection. Furnace blower assembly not balance. S making noise. No drain pan or water protection. Customer need consultation visit.
Free consultation for hvac system in Duluth Georgia 30097
One system heat tune-up in Duluth. Arrived on site, changed filterand cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found system with a dirty blower assembly, corroded evaporator coil, no water safty, filter is not properly installed, inducer motor drawing higher than normal amp. Plenums and duct work have organic growth, drip-t for gas line is not properly installed, and duct work is all R-6. Due to high cost of repairs I recommend replacing the equipment.
Replaced inducer draft vent motor In Duluth Georgia.Tested new motor and working properly at this time.
1 90% furnace in attic swapped for 80% furnace. Ran 1 6 inch supply in childâ€™s closet.
Complete heating tune up inspection for furnace in Duluth. Change filter 16x25x1, check safety and operations. Find Trane 14 year old gas furnace operating with worn ignition and missing water protection. Suggest to replace Trane ignition and suggest water protection for system in attic. Suggest surge protection and air purifier system.
One system maintenance in Duluth/ found bad induction motor / and smart gas valve/ system is 16 years old / recommend replace furnace due to age and cost of repair
Completed a three system heating maintenance in Duluth Georgia. Prepaid visit today . Checked the safety and performance of the heating operation. Checked integrity. Checked heating elements. Changed air filters. â€¢Upstairs system is heating normal at this time . The attic insulation is low and below the beams would highly suggest bringing the attic insulation to speck levels to improve efficiency and lower utility bills / comfort. â€¢Main floor furnace has high amps and the internal lube for the bearing for the inducer motor is drying out and making a loud running noise . Would highly recommend replacing the inducer draft motor to prevent future issues. Took video of noise and operation. There is biological growth all in the air plenum for the main floor and causing the system to get dirty and cause the air flow quality to go down tremendously, would highly recommend a UV light in the system to kill and prevent the biological growth from spreading . Took pictures. â€¢Basement s
Sign 2 comfort control maintenance plan and complete heating maintenance in Duluth. Change both filter, check safety and operations. Complete combustion calibration service for both Lennox gas furnace to help improve temperature and efficiency. Need to keep check on upstairs furnace flame sensor. Both gas furnace operating with in manufacturer spec.
Complete heating maintenance in Duluth. Check and find 5 year old Lennox gas furnace operating with weak capacitor, weak flame sensor and under fire and only at 79% efficiency. Complete combustion calibration service t improve temperature and efficiency, replace warranty flame sensor and warranty capacitor.
Complete heating maintenance in Duluth. Change filter customer provided, test safety and operations. Find 5 year old Lennox gas furnace operating with in manufacturer spec. No concern on furnace. Check steam humidifier for customer. Suggest pureAireX air purifier and surge protection
Two system heat maintenance in duluth. Arrived on site, checked filters and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found upstairs system without secondary water safty. Recommended installing in addition to surge protectors for each unit. Both systems are operating normally at this time. Also recommend installing the first step of Indoor air quality being an electrostatic air media.
Complete 2 heating Maintenance in Duluth. Find 2 7 year old Lennox gas furnace in attic operating with in manufacturer spec. No concern on both furnace. Change filter, clear pressure port, check safety and operations. Suggest in-line water protection for both system in attic and suggest surge protection for furnace.