My AC stopped working in this terrible heat wave. Vu came to the house and had it all fixed in an hour! He was very friendly, professional and knowledgeable.
Very professional and friendly technician
I am very happy with his knowledge
The Comfort Control Consultant was very knowleadgeable and very customer service oriented when explaining and providing all of the potential options available for a new HVAC unit for our residence.
Great company! Steve and company worked with me to make everything perfect in my studio workplace. Replaced a faulty system. Love that I could have heat/air without any ducts! Great people, reliable company. Would recommend!
I’m very pleased with his knowledge of the problem!
Heat operation normal. Discovered concerning amounts of mold in downstairs system. Need to return to install Antimicrobial Ultraviolet System to combat mold growth and also to replace humidifier pad. Paid in full
Completed 3 system maintenance. Found main and basement unit working good with drain pan switch tied to condensate pump. Switches working properly. Changed filters. Blowers are clean. No signs of growth in systems or ductwork. Both ignition controls all working good and cleaned. Recommend inline float switch to prevent water damage to furnace. Customer declined. Upstairs unit is 20+ years old and has very dirty blower wheel as well as weak capacitor and over stressed induced motor. System also has signs of corrosion on evap coil and definite signs of mold around system. System needs to be replaced as well as having an air purifier installed to cleanse the air and prevent harm to reaidents.
Quoted to do duct cleaning. Gave options for filter system and air purifiers.
Complete 1 system furnace repair and preventative maintenance check. All furnace components working good and clean. Capacitor is a little low and may need replacing if gets any lower. Recommend pure air filter for better filtration. System heating properly.
Complete 1 system furnace repair and preventative maintenance check. Found main level heat pump has bad txv. Capillary for bulb has snapped off. Need to replace txv. Will schedule to come back out next Thursday to replace.
Complete 1 system a/c repair and preventative maintenance check. Installed float switch. Tested and it turns off system appropriately. System is cooling.
Complete 1 system furnace repair and preventative maintenance check. operation normal at this time. The homeowner still does not want and repairs for mold or compressor savers
Completed 2 system maintenance found both systems running good with clean blower wheels working safety features and clean filters. Recommend pure air package to better clean the air in the house and kill bacteria allergens and odors.
Complete 2 system furnace repair and preventative maintenance check. Found upstairs unit with UV light surge protector and secondary water switch. Blower wheel is clean all electrical components are good and system heating good. Basement system is heating good with clean blower wheel and working electrical components however system has no secondary water safety device or surge protector. Also system has no air purifier device installed. Recommend all 3 to better protect system,house, and residents.
Complete 1 system a/c repair and preventative maintenance check. Found drain line very clogged. Recommend inline float switch on main drain line to prevent water from going down into drain pan. System is cooling.
Complete 2 system a/c repair and preventative maintenance check. Found main system 2 years old running good. Recommend a pure air system to purify the air in the house killing bacteria allergens and mold. The side house system is 15 years old has a dirty blower wheel and low power capacitor. Recommend getting a quote to replace the system due to age and inefficiency. Systems cooling at this time.
Complete 1 system a/c repair and preventative maintenance check. Found bad motor controller in the condenser. Replaced and restored cooling.
Complete 2 system furnace repair and preventative maintenance check. found upstairs air handler with no p trap and only drain pan float switch. Recommend inline float switch and p trap for proper condensate removal and water protection. Main level furnace has no form of water safety recommend inline float switch and water sensor for optimum water safety. Both system running with standard 1 inch filter. Recommend electro static filter for optimum filtration and to keep blower and evap coil cleaner longer. Also recommend inhibitors for both systems to prevent bacteria, allergens, and micro organisms to live in systems and spread through the house. Which would cause sickness in residents.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at email@example.com or call us at (770) 932-5012.
Found system out of charge. Leak searched and found leak in condenser coil. Recommend replacing system due to age. Setup for Comfort Advisor to come out and give options. Schedule between 12-2 today.