We had great service today from David Domercant. He came out on Fathers Day and diagnosed the problem. Hopefully we will get our much needed part ASAP. Thank you Comfort Control Barbara J Case
Good technical support, but left our fence gate open, had to chase our 2 dogs home.
Good timeline for the service and on time.
Excellent and efficient service. The technician arrived early, assessed the problem and provided recommendations. The problem was fixed!
Five times to come out to fix an AC is a bit much, but he did try to keep us up running with coolent even thought it kept leaking off. He's a nice young man and he's still young and learning but I think he will become a good tech
I have two AC systems, one Amana and one Trane. Comfort Control does the maintenance. The service tech I use does an awesome job. Very thorough and very knowledgeable about his work. Highly recommend!
Install 2.5 Ton Goodman heatpump system. Repair suction line at wall. Install hard start kit. Pressure test and recharge system system to manufacturer spec.
Performed 2 ac pm, both system operate fine, checked blowers components, changed filters, checked drain lines recommended overflow protection on us system, installed compressor saver on the DS system, checked ac components, operating pressures, cleaned outdoor coils.
Military Discount. Installed new 3 ton Heat Pump System. Vacuumed and balanced charge.
Estimate for new heat pump
Return to get HP information
No cool. Found condenser intermittently failing due to damaged low voltage wiring. Repaired wiring and system is cooling at this time.
System was not cooling due to considerable loss of refrigerant, found leak from reversing valve, took photos and videos of leak. System is 13 years old, customer wants a qoute on heat pump replacement, we recently replaced the evaporator coil. Will follow up
Breathe easy package- special note, if this system doesnâ€™t solve the issues we will remove and no charge to the homeowner.
Quoted new 3 ton Heatpump. Located in the basement.
Found low volt wire grounded going to condenser set. Ran new wire from condenser to furnace. System is cooling.
No cool. System stayed on, found system stayed on cool. Found miss wire, rewire thermostat and system now working normal
Estimate for Breathe Easy bronzer package
Completed diagnostic found compressor not getting enough power for initial start up. Installed hard start kit to fix problem system is running at this time.
No cool. Found bad condensate pump. Replaced it and system is cooling at this time.
In line water safety was hooked up to secondary drain pan port and was capped off. Water was filling up secondary drain with safety and tripped even though primary drain is completely clear. I switched the safety to the primary line. System operation normal at this time