Tune up Gainesville. Customer had water leaking out of indoor unit. Found it was due to a clogged condensate trap. Water had backed up into drain pan and soaked the insulation. Replaced condensate trap. Changed filter. Blower wheel is clean. Drain line is clear. Did not find any leaks on evaporator coil. Outdoor capacitor is within range. Pressures are within range. System is cooling at this time.