Reese was on time, friendly and knowledgeable.
I love when service providers are on time, complete maintenance efficiently, and are professional when interacting with me. Comfort Control never disappoints!
Ta did a great job explaining the problem with our system and getting it resolved in a timely manner. As always he was very polite and courteous.
Very thorough job, really did great explaining everything he found
Ta always does an awesome job and is so good to explain everything to us.
I was happy that Comfort Control provided me a very competitive quote for a completely new system (furnace and AC), as I've had a long-term relationship with the company, and did wish to change vendors. I appreciate that the owner, Tom, personally came out to conduct a quality control inspection about a week following installation.
We installed a new furnace in the basement for the Mainfloor. The system has been set in a new water pan and has two water detection devices. I put in a new condensate pump. I collected the $2208.
Completed maintnenace on all 3 systems. Found main floor unit with inducer motor with weak bearing causing loud noise. All units are operating normal at this time.
Gas valve turned off and pilot not lit. System operating properly at this time.
Performed 3 system heating maintenance. Both whirlpool furnaces need blower wheels to be chemically cleaned to restore balance and efficiency. One whirlpool system has overflow switch, highly recommend installing a second one on the other system as well. Newer Lennox unit needs surge protector to keep electrical components from damage. Added bleach to all drain lines and condensate pumps. Homeowner has already recently changed. Surge protector $212.5. E-z flow switch $169
Found bad ignition system, completed job HM2-A Single Ignition System Repair 3 month warranty Due to overall condition and age of unit recommmend replacing system but unit is heating at this time. Recommend apco air purifier due to tar on coil from smoking in home and mold growing in plenum.
2 furnace pm check complete. Changed filters. Tested mechanical and electrical components, all in good shape.
1 system furnace renewal. Replaced filter, checked electrical and safety switches all ok at this time.did a combustion calibration for furnace. System was running hot, tested and system heating normal
2 system furnace prepaid pm. Replaced filter, checked electrical and safety switches all ok at this time. Both system heating normal. Suggest apco uv light for bacteria and mold prevention.
3 system furnace prepaid pm. Replaced filter, checked electrical and safety switches all ok at this time. Main floor heating normal, upstair needs a combustion calibration. Owner wants to wait. Basement system heating normal
3 system furnace renewal. Upstair, main floor is the renewal and the basement is preapid. Replaced filters, checked electrical and safety switches all ok at this time. Tested both furnaces combustion and all within range. All 3 system is heating normal
2 furnace pm check complete. Did not change filters. Changed upstairs water panel. Tested mechanical and electrical components, all in good shape. Combustion readings are good. Systems heating normal at this time. Recommend surge protection to protect furnaces from power surges.
Performed 1 system heating maintenance. Furnace blower wheel has large amounts of dirt and grime build up and needs to be chemically cleaned to restore balance and efficiency. Black mold growth in supply plenum. Recommend u/v lighting system to kill mold and bacteria and clean the air.
1 heatpump pm check complete. Did not change filter. Tested mechanical and electrical components and found voltage absorption system running weak out of specs, recommend repair. It is still functional but out of specs. Replaced voltage absorption system, subtracted $75 off for labor warranty, customer is paying $199 for the part since the last part was still functional. System heating normal at this time. Renew cci plan.
No heat. Found system tripped on flame roll out. Found worn ignition. Found dirty blower housing.reset and system still not working. Owner wants to wait on repairs