Friendly great timely service
Everything is working fine on my new system purchased from Comfort Control about one and one half years ago. The maintenance visit was great: on time, professional, and good communication.
Very professional & knowledgeable tech
Heat pump went out and Comfort Control provided quick response with professional and courteous service and repairs made by Reece Wilson! He went the extra mile to be sure we understood the problem as well as the billing, instilling confidence and appreciation.
My heat wouldn’t come on, Comfort Control sent Reese out same day. He diagnosed problem, offered options as well as a single solution. I have received nothing but the best in courtesy, professionalism, excellent product knowledge, patience and kindness from Reese. He’s the best!
Pleasant, knowledgeable and extremely competent. He knows his business. Excellent service, as we have always received from Comfort Control!
1 system A/C preventative maintenance check completed. The customer wanted simpler thermostat so I replaced the existing one with a Honeywell T4 Pro and set it up as non-programmable. Changed filter. Found burnt main electrical switch and replaced it. Chemically washed condenser coil. Recommend hard start kit to reduce load on compressor to prolong the life of the system. System is cooling at this time.
Military discount. Install water heater in basement.
Completed 2 system maintenance found upstairs unit to be older and have a condenser fan motor with bad bearings both systems have dirty blower wheels. Cleaned both wheels. Customer would like estimate on new ac system for upstairs.
Duct board supply boxes have mold growth. Atlanta air duct cleaning is going back to clean it. All the duct work in the attic is owl flex which was recalled back in the early 90â€™s. If this continues to happen the only way to fix it is to replace all of the duct work.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at email@example.com or call us at (770) 932-5012.
2 system A/C preventative maintenance check complete. Changed filters. Tested mechanical and electrical components, found no issues. Highly recommend hard start kit for main level system to reduce load on compressor. Installed a hard start kit in the main level system. Systems are cooling at this time. The customer used $35 off coupon
3 system ac preventative maintenance check complete. Left replacement filters. Tested mechanical and electrical components, found the main level condenser fan motor bad. Ordered a new one and will return to replace it later under warranty. Chemically washed condenser coils. Systems are cooling at this time.
Two system ac preventative maintenance check complete. Changed filters. Added chlorine tablets to evaporator coil drain pan upstairs and condensate pump downstairs. Tested mechanical and electrical components, found no issues. Chemically washed condenser coils. Recommend hard start kits to take a load off of compressors to help them run smoother and last longer. Recommend surge protection to protect units from power surges. The systems are cooling at this time.
One system A/C preventative maintenance check completed. Changed the filter. Added chlorine tablets to the condensate pump. Tested the mechanical and electrical components. Found a weak blower capacitor. Found no water safety so I recommended adding it on. Chemically washed the condenser coil. Replaced the blower capacitor and installed water safety measures. The system is cooling at this time.
One system A/C preventative maintenance check completed. Changed the filter. Tested the mechanical and electrical components. Found a burnt main electrical switch and a weak capacitor. Changed the parts out under warranty, but the labor is not under warranty. Installed secondary water safety measures. Chemically washed the condenser coil. Cleared the drain line. The system is cooling at this time.
2 system ac prepaid pm. Replace filter, cleared drain and clean condenser coils. Smell gas leak outside at the gas meter( homeowner is now aware of the gas leak). Installed compressor saver for both Ac system. Both system is cooling normal at this time
Adjusted return air grills to stop the air noise.
2 system A/C prepaid preventative maintenance. The air cleaner is good. Cleared the drain and cleaned the condenser coil. Recommended to add a compressor saver for both A/C systems to help on startup and to put less stress on the system. Both systems are cooling normally.
One system. Cleaned the upstairs unit. She will go with our membership after Shumares runs out.
1 system A/C preventative maintenance check completed. Changed the filter which the customer provided. Cleared the drain line. Tested the mechanical and electrical components. All are in good shape. Recommended adding a hard start kit to reduce the load on the compressor and to prolong the life of the system. Recommended adding surge protection to protect the unit from power surges. Chemically washed the condenser coil. The system is cooling at this time. The customer used a $50 gift card.