Brian came promptly to my home and he gave me a courtesy call before he came. He had to diagnose where the source of the air flow to a certain vent in my basement . He methodically looked at what needed to be done giving the circumstances that particular vent is in a finished part with sheet rock. He had explained everything to me and showed me that he was unable to rectify the issue without cutting into the Sheet Rock. I decided to leave everything as is and my system still functioned well. Brian left his work site clean, he followed CDC guidance and he was polite. I would recommend Brian to provide service to anyone because his approach to rectifying a problem was through, methodical and with high quality.
Called on a Sunday morning of Labor Day weekend. Reece Wilson texted us and arrived in less time than what he estimated. Inspected all the units and diagnosed the issue. Explained everything he was doing and why. Had all the history of our system on his tablet from previous services. Thanks Reece for the great service. Highly recommend this service team !
Jon Fowler was on time for our service call and got a text with his picture attached and phone call saying he was on the way. He went through checking our two HVAC units and explained what heats doing and his recommendations all through the visit. He seemed very knowledgeable and polite. For COVID-19 compliance, he wore a mask and had put on boots as well I appreciate his help and knowledge.
Reece was very helpful and went through ecobee set up
Very astute. Clear offered good alternatives. Pleasant manner
Detailed and knowledgeable
Jon Fowler came out as an emergency service call and he was very much in line with the CDC Guidelines and wore shoes protection as he entered our home. He systematically checked everything to confirm that there weren’t any similar issues. He was able to identify the issue and quickly resolved the problem. Jon was very polite and courteous and I would highly recommend him.
Eric is part of Tom Kohberger crew of amazing, talented and awesome techs who came to my house to install an amazing Daikin VRV System with multiple Air Handlers.
Complete heating maintenance for Lennox 5 year old system in Lawernville. Change Aprilaire 610 filter, check operations and safety. Find furnace heating system operating with in manufacturer spec. No concern at this time.
Estimate for new system in Lawrenceville
Ac warranty in Lawrenceville. Found float on float switch stuck, fixed it and system is operating at this time.
Dental office is Lawrenceville Georgia is having HVAC problems . â€¢Unit is making a very loud noise and vibration took video . The fan motor is seizing up and over heating . Also the frame off this system is falling apart which is another reason with the vibration... would highly recommend a new system at this point due to age and conditions. Repair option would be to replace the fan motor . Gave options . â€¢Also found a ton of biological growth growing on the blower wheel took pictures. This is not good for the air quality nor for the equipment. Would either recommend replacing or pulling the wheel out and completing a deep chemical wash on the air movement system . â€¢Heat exchanger has cracks which is a huge safety issue Iâ€™m going to have to turn the gas off at this system . Wrote down cracked heat exchanger and turned gas off to the valve . â€¢Would highly suggest having a consultation for a new HVAC system . â€¢After installing the new fan motor the compressor was n
Remove and replace all existing and accessible flex from the upstairs system in Lawrenceville
One system heating maintenance Lawrenceville, arrived on site, changed filter and checked electrical connections, amp draw on motor as well as heat exchanger. Checked pressures for refrigerant circuit as well as electrical connections, amp draw, and capacitance on heat pump. Unit is operating normally at this time
Complete 2 furnace heating maintenance in Lawrenceville. Change 2 16x25x1 filter. Check operations and safety. Find both 26 year old Lennox furnace operating in poor conditions and overheating and intermittent shut off on high limits. Find both upstairs blower motor worn and leaking oil. Fin s blower wheel very dirty and blower motor not running at full speed. Find flame sensor weak, find air pressure sensor worn and not pulling in properly. Inducer assembly worn and furnace chamber rusting. Both furnace also operating with high CO level and not safe to operate per NCI Safety guide line. Downstairs flue pipe PVC, not code and need to be double wall flue pipe. Due to system conditions, furnace need to replace replace and not repair.
Ac repair in Lawrenceville, Georgia. Found system with bad thermostat. Replaced thermostat and system is cooling at this time. Found evaporator coil very rusty and corroded and therefore likely to leak. Found blower wheel to be dirty. Found dual capacitor to be weak. Customer used $50 coupon.
Basement is finished and had no way to trace that air duct . Family did not want to bypass that register and cap it off . So I left the register alone . Warranty today . Thank you .
Ac service lawrenceville. Completed diagnostic. Found system void of refrigerant. System is 24 years old with very dirty blower wheel and rusted evap coil. System running on r22. For better efficiency and financials system needs to be replaced to newer refrigerant. Having jim come out to give quote.
Replace Lennox manufacturer warranty compressor, with hard start kit and CCI plan. Per Jeff, flush line and replace line dryer. Pressure test and vacuum system to 500 micron level. Recharge system to manufacturer spec 8.5 lbs R410. Test and system operating at this time. Complete cooling pm check and change both filter.
Ac repair in lawrenceville. Replaced damper motor for downstairs. Tested and operation normal at this time.
No cool Lennox system in Lawrencevlle. Check and find upstairs 2 year old system with clogged system and inline water protection shut off ac unit. Flush drain for air conditioning unit. System operating at this time. Suggest hard start kit, CCI maintenance plan and surge protection for outdoor.
No cool upstairs Lennox system in Lawrenville. Check and find bad compressor. Need to replace warranty compressor under warranty but not labor
No cool in lawrenceville, arrived on site, customer states that upstairs kids rooms get hot. Suspect zoning issue. Thermostat is in Masterbedroom on opposite side of house. Checked electrical connections, amp draw and capacitance. Checked refrigerant pressures and state of system. Unit is operating normally at this time.