5 Star as always.
Very pleased with Christian he was very professional and ver knowledgeable about his job!
Brian showed up on time and also gave me a curtesy call before he arrived and once he arrived he was well equipped by complying with mask respectively. Brian inspected all my indoor units and also verified calibration of all indoor units and also checked the outdoor unit for performance. His overall performance was outstanding and I would recommend Brian to provide service to anyone. Hey Tom, you have a team of some excellent employees and my family & I wish you, your family and your employees to continue to provide excellent service to your customers. Thank you very much.
Chris was very polite & professional. I was very pleased with his service.
Vu Tran always does a great job. Extremely professional.
Was hoping for a simple fix, but what the tech showed me, it was was not. He quickly got the parts and replaced the worn component and offered some solutions to avoid the issue again. Very nice, polite and quick to get the problem solved.
Vu is always on time and explains everything he does in an easy to understand mode!
The check up was performed on time, and completed thoroughly and efficiently. The recommendations were consistent with previous visits. Reece is a very personable guy.
No heating main system. Sign cci plan, install pureAireX air purifier system to kill bio growths and improve air quality. Clean flame sensor. Complete heating maintenance inspection. System operating with in manufacturer spec.
Heating repair in lawrenceville. Discovered system having intermittent ignition issues. Cleaned pressure port and system started heating. System is in extremely rough condition and replacement is highly recommended. System heating at this time.
No heat lawrenceville. Completed diagnostic. Found thermostat had been locked out and reset. Unlocked thermostat. Turned system on. System heating at this time.
call back in Lawrenceville. Arrived on site, found drain line has come loose again. Re cut line and extended further to that there is now pressure on coupling going into vent pipe then glued coupling to vent. Tested system, no issues present at this time
Replace flu to furnace. Replace evaporator coil. replace supply plenum. replace 5 sections of flex ducting replace exposed drain line replace flu caps on roof replace venting cap for bath venting
Two system heat maintenance in Lawrenceville. Arrived on site, changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found both systems have ductwork that is undersized for the unit recommend installing more on both supply and return. Unit in crawl space has no water safty and I recommend installing surge protection to both systems. Unis are both running at this time.
Repair lawrenceville. Completed replacement of control board that was damaged during flooding. System is heating properly.
No heat in Lawrenceville/ found bad gas valve under 10 year warranty/ replaced and tested
No heat lawrenceville. Completed no heat. Found system not heating very well found low on refrigerant. Could not find leak anywhere in coils or inside unit or at valves. Filled with 410. System heating at this time.
Complete heating maintenance for main level gas furnace in Lawrenceville. Did not change filter, check safety and operations. Find Lennox gas furnace under-fire and not calibrated. Complete combustion calibration service to increase temperature and efficiency. System operating at this time. Suggest surge protection, in-line water safety and air purifier.
Repair lawrenceville. Could not get furnace running found issue at control board due to water damage. Need to order board and return to replace it.
â€¢Heating issues at the Dental office in Lawrenceville Georgia. 12/1/2020. â€¢Package system has a cracked heat exchanger and causing the system to roll out on the burners . System is not safe to operate in heating mode . Turned system off at the shut off valve on the roof top . Took video of the burners . Would highly recommend replacing the equipment. Along with the draft motor failing and making noises . Took video of the noise . Dental office is going with replacing the equipment. Going to schedule the replacement. Will schedule install and get the project started . Office will call and keep update on the date for the install . â€¢Waiting room / reception room . System is frozen on the heat pump outside. Going to look into that issue as well . Other system is low and causing the system to freeze up . Would highly recommend a leak search and see where the equipment is leaking ... or recommend charging the system back to specks and see how it holds up and determine if itâ€™s a b
Repair lawrenceville. Completed replacement of air handler control board. System came on. No fuses blown. Ran for 10 min. System heating at this time.
Water leak/call back in Lawrenceville. Arrived on site, found the condensation drain line had come out of the vent pipe and had been dripping into the wall because it was too short. Extended the line with extra pvc and secured fitting at the vent. Tested system unit is draining properly
Heating maintenance lawrenceville. Completed maintenance on 2 10 year old systems. Upstairs is running good. Everything clean. UV light and filter are good. All safety switches working. Insulation is spray foam. Drip leg is installed for gas line. Basement system has had water damage from main floor basement flooding. Furnace is clean but pressure switch has failed. One long run of duct needs to be replaced. And evap coil is very rusted. Should be replaced as well. Will send estimates for those three to customer.