Arrived on site for annual safety and maintenance inspection. Tested all fixtures for proper drainage and function. All under sink waste piping is free of leaks and all fixtures are receiving satisfactory temperature and pressure. Did not exercise plunger style emergency stops per homeowner request. Provided option for replacement of all plunger style emergency stops in the home. Customer has a lavatory sink with a slow drip. Provided options for replacement of cartridge as well as replacement of faucet. Inspected crawl space for signs of leakage, rodents and to assess condition of sewer main and water piping. All visible water piping in crawl space is insulated and sewer main is in good condition. Drained and flushed hot water heater, then purged air from the lines at fixtures. Set water heater back to existing temperature setting. Thank you for choosing CPI Plumbing & Heating!