Arrived onsite to perform annual safety and maintenance inspection. Began by testing my inlet gas pressure which gave me a reading of 8.43. Tested my blower and was pulling 1.52A. Tested for CO found none. Measured for my delta T and got a air temp differential of 56 degrees. Insured unit was working properly upon leaving.