Arrived on site. Shut off and drained hydronic heating system as required. Provided installed new zone valves with actuators for entire home. Provided spare valve components as per customers request. (Located in mechanical room). Stored water system. Tested at working pressure. Purged air from system. Filled mini feeder with water. Confirmed operation of indirect water heater. Cycle tested twice. Confirmed operation of heating system. Set all thermostats to 70* F. Tom will return to confirm operation, check water level in mini feeder, and lower thermostat settings. Thank you for choosing CPI plumbing and heating Inc.