Arrived onsite customer had informed me that she had a leak. Discovered that it was coming from the temperature and pressure relief valve as it had failed. And the dhw expansion tank had failed also. Presented pricing customer approved the pricing. Performed work. Discovered a small leak on the boiler expansion tank presented pricing customer approved, so I performed the work. After I swapped out those parts I filled the system up to 15 psi, turned power on to the boiler. And had the customer confirm that she had hot water, and had them give a call for heat. Customer informed me that she had hot water, and I watched as a call for heat on the heating side of things was performed. No error codes or failed attempts at a call for heat. Thank you for choosing CPI Plumbing and Heating Inc.
Customer had a complaint of a leaky relief valve. Arrived onsite took a look at the issue discovered that the expansion tank had failed and the relief valve had failed also. This was causing the relief valve to constantly pour out water. Provided pricing to make the repairs. Customer approved so I began work. Removed and replaced both the relief valve and expansion tank after isolating and draining down the system. Opened up all valves and filled the system back to working pressure. Bled any air. Fired up the boiler checked that the DHW was working properly, checked all heating zones as well. Boiler was operating as should discovered that the boiler did not have an approved back flow prevention device, also noticed that the gauge on the top of the boiler had frozen in place, the fill valve to the boiler was not filling at the correct speed, provided pricing for these repairs, these are not required to make the repair for today but I would recommend these additional repairs to keep the
Met w/customer and drew water sample. Water test results Hardness 10 Grains Iron .25 PH 7.5
Arrived onsite to perform annual safety and maintenance inspection on customers Boiler. Did an inspection looking at all components, making sure all measurements were within the correct thresholds, and in good condition. After taking a look around I noticed that the condensate trap was cracked, provided pricing to replace it. Customer signed off so I did the work. This issue is fairly common in Buderus GB124 boilers. Overall boiler is in good condition, and working as it should. Thank you for choosing CPI Plumbing and Heating Inc.