Atmospheric 40 Gallon Water Heater Installation Turned water off fully to tank before beginning This is just a straight replacement tank Confirmed the tank was fully isolated and the gas was off Connected transfer pump to bottom of tank Disconnected water supply lines on top of unit Removed earthquake straps Disconnected gas flex line Disconnected vent piping Removed tank from build (for disposal back at shop) Had to go to warehouse to get a short model tank Unboxed new Bradford White 40 gallon natural gas atmospheric tank Cleaned area under old tank Removed old body straps from wall anchors Had to create a support for the earthquake straps, had to drill and set anchors in concrete Secured new body straps at new height locations to match new tank Installed new thermal expansion tank Pumped thermal expansion tank to 70p.s.i. to match with the house Set tank in location and secured to wall with earth quack straps Connected new stainless flex supplies Turned water back on and filled ta
Arrived onsite per customer complaint of their AC not working. Upon arrival William let me know that the unit was not functioning correctly and not producing cold air. Provided a price to do a diagnostic. As well provided a price to replace the unit. Customer declined both options. CPI did not charge a dispatch fee. No work was performed at this time. Thank you for choosing CPI plumbing and heating Inc.
Gave pricing for work that was requested in pumphouse regarding water system
Arrived onsite customer has a water heater doing domestic hot water and radiant heating, presented pricing to the customer to inspect the system, customer declined pricing and was unhappy with the cost.
Checked customer complaint about a clogged kitchen drain line. Presented customer pricing to attempt to clear the drain line with an auger. After pricing was approved I laid down a rug to protect the customerâ€™s floor from damage. Performed augering of drain. After augering for a while I was unable to clear the drain. Performed crawl space inspection of the kitchen drain line. Discovered the drain line hade multiple bellies and deformities. Presented customer pricing to repipe the kitchen sink. Customer requested the estimate be sent to his email. The estimate was emailed before my departure. CPI does not warranty or guarantee drain cleaning. Thank you for choosing CPI Plumbing and Heating.
Checked customer complaint about old manifolds. Customer had two manifolds made of copper and he requested pricing to replace the existing manifolds with plastic ones. Presented customer pricing to replace the existing manifolds with new ones. Customer requested the estimates be sent to his email. A dispatch fee was collected at this time and the estimates were sent to his email before my departure. Thank you for choosing CPI Plumbing and Heating.
Customer called about a leak under the sink. Upon arrival I could see that the p-trap had broken apart and was leaking into the cabinet. There was also a back graded section so I offered to redo the under sink waste pipe. Customer accepted. Removed previous waste pipe and installed new piping up to the trap arm. Tested installation by doing 5 drain down tests on both sinks simultaneously. No leaks detected. Thank you for choosing CPI!
Confirmed with customer that one toilet is having constant blockages and overflowing over the last month and tank to bowl is loose. Also leaking hose bib customer has replaced gasket inside and is still leaking. Provided estimate to camera mainline and check septic tank customer does not want to camera mainline at this time. Removed toilet didnâ€™t find anything blocking flange or bottom of toilet. Removed all old components inside toilet tank and replaced with new tank to bowl gasket, bolts, fill valve supply line and replaced wax seal at flange. Tested verifying proper function and no leaks present. Had to open drywall in garage to access hose bib. Turned water off to building and Removed old leaking hose bib. installed new frost free hose bib Tested verifying no leaks present. If toilet continues to back up suggest getting mainline inspected. Thank you for choosing CPI Plumbing and Heating.
Left option to run gas line to range Left option to install recessed box valve and sediment tee Install includes pressure test Left option to install owner supplied range Owner wants time to review options 1/2 down deposit through office to schedule and perform work as quoted
Performed work as proposed isolated water to recirculating pump. Customer was not getting hot water for over 3 minutes at each faucet. Removed old pump and installed new ball valve in order to purge air out of the lines when installing new pump. Installed new pump and purged water lines of air. Plugged in power for pump verifying proper function and no leaks present. Tested kitchen faucet and farthest bathroom faucet from water heater now getting 130 degrees after 10-20 seconds. Thank you for choosing CPI Plumbing and Heating.
Arrived onsite today 11/6/2020 to replace the vent damper as proposed. Isolated power to the unit. Removed all existing wires disconnected the venting removed damper and replaced it with the new one. Reconnected all wires powered on the unit. Confirmed operation of the damper and the boiler itself. Boiler was operating correctly and so was the damper. Boiler reached temperature. Damper closed when boiler reached temp. Thank you for choosing CPI Plumbing and Heating Inc.