The guys know their stuff. Very professional, Im pleased with their work, and their overall work ethics.
Technicians went above and beyond to repair my furnace
As usual it was a good service call JW is a very knowledgeable technician took care of the problem and his assistant was also dependable. The only problem was you charge too much money for what you do lots of people can't afford it.
I got very fast service. Nice tech. Just wished he'd checked the inside so I can know if anything is wrong there.
Dependable is fantastic
I've been a customer for over 10 years now. Dependable Heating & Air Conditioning lives up to the DEPENDABLE name with fair pricing, knowledgeable associates and GREAT service from repair/replacement to system maintenance. I highly recommend Dependable Heating & Air.
Excellent workers and very courteous and he and Brian did a great job, before and after completing the work.
The Technicians were very professional and did an excellent job.
Very pleased Brian's knowledge and pleasant demeanor!
GOODMAN AIR CONDITIONER CHANGE BLOWER SPEED FROM HIGH TO MEDIUM .Changed blower motor speed to medium .
GOODMAN AIR CONDITIONER GO BY AND CHECK ON CUSTOMERS REPAIRS. Upon arriving found that unit was low on charge. Checked leak on full system and found that the schrader valve on discharge was loose and leaking . Removed all the caps to check for any further leaks and removed condenser fan motor to check condenser . Checked evaporator coil and set . Tightened schrader valves and installed leak lock . Charged unit 2lbs of 410a . Cycled unit and unit is operating properly .
RUUD SPRING TUNE UP
WANTS TO EXTEND DUCT WORK IN THE BASEMENT AND GO UPSTAIRS/CUST IS SAYING 12FT
GOODMAN AIR CONDITIONER SPRING TUNE UP
CORREY REACH IN COOLER MAIN UNIT NOT COOLING needs new compressor and hard start kit
GOODMAN GOODMAN NO HEAT, NOT COMING ON PLACED THE FILTER IN THE UNIT AND UNIT IS WORKING
WANTS TO EXTEND DUCT WORK IN THE BASEMENT AND GO UPSTAIRS/CUST IS SAYING 12FT GAVE CUSTOMER AND ESTATMENT ON WHAT IT WAS GOING TO COST TO REPLACE THE DUCT WORK
PAYNE FURNACE FALL TUNE UP
WELLS FRYER THE DIAL THAT CONTROLS TEMP IS SPINNING REPLACED THE THERMOSTAT
RUDD FURANCE FALL TUNE UP
ADVANTCO VENT HOOD NOT PULLING AIR FOUDN THE FILTER NOT INSTALLED CORRECTLY REINSTALLED
ADVANTCO VENT HOOD NOT COMING ON MOST OF THE TIME REPLACED THE BELT ON THE MOTOR
TRUE REACH IN COOLER 3 DROOR - NOT HOLDING TEMP/UNIT IS OFF BY A COUPLE DEG instaled evaporator motor
RUUD FURNACE KICKING ON AND OFF ADJUSTED THE TSTAT AND UNIT IS WORKING