Another great experience with Dependable! See you in the spring.
Appreciated Brandon's professional approach and his quality of service rendered.
Brian, as always, was right on time, courteous and careful. I appreciate that fact that I know who is coming while also knowing who is taking care of units. The bi-annual inspection & service is a great option and I am glad to know that there is one less thing that I have to worry about!
ADVANTCO VENT HOOD VENT FILTER IS DISINTEGRATING AND NEEDS TO BE CHANGED.
IMPERIAL OVEN REPLACED THE OVEN
TRANE NOT COOLING FOUND THE BREAKER WAS TRIPPED RESET AND UNIT IS COOLING
BEVERAGE AIR COOLER NEEDS TO VACCUMED AND RECHARGED/ NO RECHARGE PORT ON IT UNIT NEEDS NEW SERVICE PORTS ADDED SO THAT WE CAN TEST THE UNTI FOR LEAKS
IMPERIAL DOUBLE OVEN NOT WORKING/THINKS IT HAS TO DO WITH LATCH FOUND TEH CAM THAT ACTIVATES THE DOOR SWITCH HAD CAME LOOSE ADJUSTED TEH CAM AND TIGHTEN ALL THE FITTINGS
BRYANT AC CONDENSOR UNIT NOT COOLING FOUDNT EH CAPACITOR WAS BAD REPLACED THE CAPACIOTR
IMPERIAL DOUBLE OVEN WILL ONLY HEAT IF DOOR IS CRACKED SLIGHTLY REPLACED THE DOOR SWITCH
IMPERIAL OVEN TOP OVEN IS NOT HEATING FAN RUNNING REPLACED THE DRAFT INDUCE MOTOR, TEMPERTURE LIGHT INDICATOR
TRANE FILTER CHANGE
RHEEM RTU 1 NOT COOLING CHANGED THE CONTACTOR
BRYANT SPRING TUNE UP ON AC SYSTEM
GOODMAN AIR CONDITIONER INSTALL NEW CONDENSATE PUMP
IMPERIAL OVEN TOP OVEN IS NOT WORKING FOUND PILOT LIGHT TUBING TO BE CLOGGED CLEANED THE PILOT TUBING AND UNTI IS WORKING
HTP WALK IN COOLER HINGES COMING OUT OF WALL, DOOR NOT CLOSING PROP, SCREWS COMING OUT OF FAN COVER INSIDE
MANITOWOC ICE MACHINE NO MAKING ICE NOT WORKING PROPERLY CHARGED THE UNIT AND ADJUSTED THE ICE THICKNESS