Mark did an awesome job. He made sure everything was handled before he left.
SCOTSMAN ICE MACHINE LEAKING FROM WHERE IT MAKES ICE/MIGHT NEED A CLEANING . Upon arrival unit was producing ice .Drain in the bin was clogged . Removed panels to gain access to drain and then blew out blockage with nitrogen .
TRANE AIR CONDITIONER THE NUMBER ONE UNIT THE OFFICE AND THE LOBBY NOT BLOWING COOL AIR INSTALLED NEW EVAPORATOR COIL
GOODMAN FURNACE SWITCH NEEDS TO BE REPLACED/MAKE SURE EVERYTHING IS HOOKED UP AS IT SHOULD CHECKED THE UNTI AND EVERYTHING IS WORKING AS IT SHOULD
GOODMAN FURNACE SWITCH NEEDS TO BE REPLACED/MAKE SURE EVERYTHING IS HOOKED UP AS IT SHOULD NEED NEW THERMOSTAT AND CUSTOMER WILL REPLACE
TRANE FURNACE NOT BLOWING HEAT INTO THE ROOMS REPALCED THE CONTROL BOARD AND BLOWER MOTOR
NORITZ TANKLESS WH #1READ OUT IS AT 120 BUT SHOWERS ARE NOT HOT CHECKED THE UNIT AND FOUND NO ISSUES IT JUST CAN NOT KEEP UP WITH THE WATER USEAGE
MANITOWOC ICE MACHINE PERRFORMED THE PREVENTIVE MAINTANCE
HOSHIZAKI ICE MACHINE REPALCED THE ICE MACHINE
MOFFAT OVEN IT WONT TURN ON REPLACED TEH DOOR SWITCH
HOSHIZAKI ICE MACHINE UNIT IS NOT MAKING ICE AND HAS 3 INDICATOR BEAMS & FILTERATION SYSTEM LEAKING REPLACED TEH BIN THERMOSTAT AND RUBBER BOOT ON WATER LINE
AMERST BOILER CONDENSER FAN IS NOT WORKING ON PANTRY UNIT REPLACED TEH COMPRESSOR AND ADDED REFRIGERATE
HOSHIZAKI ICE MACHINE UNIT IS NOT MAKING ICE AND HAS 3 INDICATOR BEAMS & FILTERATION SYSTEM LEAKING FOUDN TEH FLOAT SWITCH WAS CLOGGED CLEANED TEH FLOAT SWITCH
ICP AC CONDENSOR UNIT CONDENSER FAN IS NOT WORKING ON PANTRY UNIT NEEDS NEW CONTACTOR, FAN MOTOR AND COMPRESSOR
GOODMAN AC CONDENSOR UNIT QUOTE FOR 4TH FLOOR REPLACE SYSTEM
AIR CONDITIONER INSTALL CONTROL BOARD