July of 2017, a new $25,000 HVAC unit was installed. As of today, we still don't have not had a complete system. You need to rate yourself.
I have been using Dependable for years and have been very happy with their service. They always show up on time and do a great job!
Service tech called in advance and arrived in the time provided.
ADDISON AIR CONDITIONER GARDEN UNIT DEVELOPED ROOF LEAK SINCE EVAP REPLACEMENT CAULKED AROUND THE CREASE
PITCO FRYER NOT WORKIN G REPLACE THE TSTAT
HOSHIZAKI ICE MAKER THE POWER CORD HAS BURNT UP REPLACED TEH CONTROL BOARD
WALK IN COOLER NOT COOLING ADJUSTED THE THERMOSTAT AND UNIT IS WORKING
WALK IN COOLER WALK IN COOLER TEMP NOT GOING DOWN. REPLACED THE SO ANNOYED VAVLE
DIAKIN FILTER CHANGE
CARRIER SPRING TUNE UP ON AC SYSTEM
GOODMAN AIR CONDITIONER NOT COOLING AT ALL FOUDN THE OUT DOOR UNIT NOT WORKING FOUND LOOSE WIRE ON HPC REPAIRED THE WIRE
INTERNATIONAL CO walk in cooler WALK IN COOLER TEMP NOT GOING DOWN FOUND A HAIR LINE CRACK IN THE HIGH SIDE LINE SET REPAIRED THE LINE
ICD WALK IN COOLER NOT COOLING REPLACED THE EVAPORATOR COIL
SUPREMEMETAL STEAM WELLS NOT HEATING UP REPLACED TEH HEATING ELEMENT
MANITOWOC ICE MACHINE UNIT IS LEAKING WHEN WATER PUMPS THROUGH THE SYSTEM replaced teh water inlet fitting and replaced the water supply tubing
PITCO FRYER PREVENTIVE MAINTANCE
SOUTHBEND RANGE PREVENTIVE MAINTANCE
LANE VENT HOOD PREVENTIVE MAINTANCE