Robert responded quickly, on time and obviously knew his business well. He quickly repaired our heater. He was very professional, friendly and carefully explained the problem and his actions to repair it. I would recommend Fairview.
Heater was checked and repaired with in 2 hours from my call for service!!
Mr. Robert Conner was prompt, professional and extremely knowledgeable about the equipment and the needed repairs. I found him to be very trustworthy and felt comfortable with his recommendations. He explained everything.I would hire him again.
After contacting Fairview to help us with a previous company complaint, Robert responded promptly and solved our problem to our satisfaction.
I have & will recommend Fairview to all my family & friends. They were the most professional and had the best deal of all the places we checked which is why we chose them to replace our system in April. The free maintenance checks the year after are another plus. Robert was professional, friendly, and took care of the service call in a timely manner.
showed up on time...courteous and professional.
We had our A/C serviced back in June. Based on our experience, we feel that the company charges wayyyyy too much for replacement part. A US-made dual-run A/C capacitor usually can cost up to $40 bucks but yet they had charged us 10X more. We will definitely consider other HVAC shops for future A/C service.
Robert answered all of many questions. I will be dealing with him for the product I bought.
Working on a old Colman furnace in the delta mobile home park
One of our new American pride systems after the install on the roof
Looking at replacing a few Bard units
Working on a carrier furnace that had a trip to limit possibly do to a bad inducer motor
Working on a Goodman furnace that had a bad control board replaced it with new control and the furnace is now heating correctly
Working on a carrier furnace that had a bad pressure switch
Working on a Coleman mobile home furnace that had a bad pressure switch replaced it with the upgraded Honeywell pressure switch
Working on a Lennix furnace that was shutting the burners down due to a dirty flame sensor
Looking at replacing our York system was one of our new American pride systems that assembled here in the USA
Working on a Trane American Standard furnace it was tripped off on error code due to the variable speed motor was not running found it was very dirty and had the insulation from the inside the furnace sucked onto the motor after I remove this and cleaned it unit was running fine
Working on a Carrier furnace that won't heat found it had a bad pilot switch
Add to replace an upper limit switch the head failed on a Goodman furnace after PG&E had a power failure
Helping one of our install Crews put in one of our new American Pride series heating and cooling systems along with a dual-zone control system for the air flow between upstairs and downstairs