Mike did a great job.
Michael checked the furnace and found no problems. I questioned him whether I was putting in the filter correctly. He checked it for me and found I had put it in wrong side toward airflo. He took the time to get a marker and make a note on the furnace so ai would remember the correct way.
The problem was diagnosed and fixed promptly. Technician was knowledgeable and very friendly.
Replaced hot water tank
Cleaned out pilot assembly on a lennox steam boiler.
Outside boiler not working
Service oil furnace
Service on mini split
Service on mini split.