Jay was very informative and knowledgable as to the duct issues.
Response from GMC Air Conditioning Services, LLC:
Mr. Spencer, thank you for taking to the time to let us know how we're doing. We hope to have you apart of the GMC Family!
For this commercial facility in Boynton Beach, we arrived to assist with an AC not cooling. This air conditioning not cooling was addressed by our seasoned technician. Much AC repair was needed but our talented technician was able to solve the issue and get their AC back up and running.
We arrived to this commercial facility in Boynton Beach to complete some much needed AC repair that was found during the AC maintenance.
For this commercial facility in Boynton Beach, we arrived to install some parts and perform AC repair that was discovered during one of our preventative maintenance visits.
Onsite, our technician arrived to diagnose a system that just isn't cooling properly. After a full inspection of the system, we discovered that the liquid line dryer was restricted. Once fixed, this system will be back to cooling correctly and uninterrupted.
For this commercial facility in Boynton Beach, we arrived to complete AC repair requested by the customer. These systems need consistent maintenance and upkeep as they are powering a childhood facility, GMC is committed to taking care of every customer's needs to keep them cooling and comfortable.
For this commercial facility in Boynton Beach, our technician arrived to address an AC not cooling. After our technician arrived to perform a full diagnostic of the system, there were some much needed AC repair that needed to be addressed.
For this commercial customer in Boynton Beach, our technician arrived to address an AC not cooling and an AC blowing cold air. He discovered that there were a few faulty parts that needed AC replacement. Once completed this system was back up and running.
This commercial call was for their entire back building fleet shutting down. Onsite out technician surveyed the scene to be sure of the problem, he discovered that the duct fire alarm had been triggered and the fire department needed to be called to reset the detector.
For this commercial customer in Boynton Beach, our technician arrived to perform some much needed AC repair. Our technician replaced the blower motor and wheel apart of a quote that had been approved by the client. The installation of these parts has returned the AC unit to cooling quietly and efficiently.
We arrived at this commercial customer's facility to perform some needed ac services and ac repairs including replacing all belts and cleaned condenser coils.
We arrived to a system not cooling at a customer in Boynton Beach. After we reviewed the entire system, we were aware that some AC repair needed to be done. We reset the float switch, unclogged the drain line and topped off the freon.
We arrived to perform our schedule maintenance for this commercial facility in Boynton Beach. We performed the needed maintenance produces determined by our Service Manager when creating this custom service plan. Onsite we found a few things that need to be address, including a refrigerant leak and a few parts that will need to be replaced to avoid a breakdown. These things were discovered before a breakdown because of preventative maintenance.
During this residential routine maintenance in Boynton Beach, we performed a precision tune up and complimentary fertilization of their system. Having regular service helps prevent ac repairs and ac breakdowns.
During this service call, we addressed a system not cooling at a commercial facility in Boynton Beach. The system is in good shape overall, but the capacitor was faulty causing the compressor to shut off due to being overloaded. Once we replaced the capacitor, we checked the system for and it resumed proper operation.