We arrived at this commercial customer’s facility to diagnose and correct an ac not cooling. The system’s drain line was clogged and the auxiliary drain pan was overflowing. After correcting both of these issues we were able to move forward with the rest of the diagnosis. We also found that the evaporator coil and blower wheel were very dirty. Due to the age of the system, we do not recommend ac repair, we recommend ac replacement.