Arrived to check this system in Hallandale Beach for no cool and blowing warm air. Found that the system was not cooling due to a clogged drain line, due to lack of maintenance. After clearing the drain line and drain pan, we added gel tabs to prevent algae from building. System is now running and cooling properly. This customer signed up for service agreement and will now have maintenance every six months.
We arrived in Pembroke Park to address one of their systems not cooling, we discovered that this system is only running one one circuit causing the system to struggle. Once some AC repair was performed in Pembroke Park, this system was up and running.
We arrived to this commercial facility to address an air conditioner not cooling properly, while onsite our technician discovered that the float switch needed to be replaced and that there was some short circuiting in this Carrier system. Once the AC repair was performed this system is back up and running.
This customer was having issues with her AC leaking water in Hallandale Beach. While onsite our technician discover that it was due to lack of air conditioning maintenance in Hallandale Beach
For this commercial facility in Pembroke Pines, there was an issue with their system in the conference room. The system was very dirty, after some much needed cleaning this system is back up and running.
We arrived to this commercial facility for their scheduled maintenance that has been customized for their system's need. We changed the filters, cleared the drain line, checked all key components, electrical and safety features. These maintenances are crucial to the life and longevity of your system and the prevention of costly breakdowns and AC repair.
During this ac repair for a commercial customer in Pembroke Park, we performed a full diagnostic of the system, we discovered that the coils need replacement due to flaking and being stuck to a loose fin. This system also needed a new fresh air return metal filter.
New installation from a 17 year old system. This customer will benefit with the summer fast approaching and energy savings that will pay for the new equipment.
Quality check new install of a Carrier System with Easy filter access, Located at the beautiful towers of oceanview east located in Hallandale Beach Florida.
Ac system replace air handler unit high efficiency
Ac replace new air handler unit high efficiency
Ac system replace condenser unit and air handler unit
Prevented maintenance at ABC cleared drain line and check unit for proper operation.
Unit is not turning on. Unit has no power and needs an electrician to find power source. This is a great reason to always check your breaker before calling for service!