For this commercial maintenance in Lauderdale Lakes, we arrived to change the belts, filters and to check all the systems for proper operation.
We arrived in Margate to complete some much needed AC repair approved by the customer.
Arrived to install new smoke detectors power wires, and shut down wires on all units. Once all parts were installed checked each unit to make sure they were shutting off on smoke alarm. All units are now working properly with fire alarm panel.
This commercial facility in Lauderdale Lakes was having issues with one of their YORK systems. With the air conditioner not cooling, this was causing some their facility to become very hot. Once our technician was onsite, he was able to change the fuse and get the system back up and running.
For this commercial facility in Lauderdale Lakes, we arrived to preform maintenance on their fleet of YORK systems.
We arrived to this commercial customer to fix a system that was leaking from the ceiling. After our technician arrived and ran a full diagnostic of the system he discovered that this was a maintenance issue and was able to clear the drain line to cure the leaking.
After completing the preventative maintenance on your unit, we found a few repairs that we highly recommend getting done before the summer months to ensure your unit stays cooling efficiently.
For this commercial customer in Margate, we arrived to finish the scheduled routine maintenance on this facility's HVAC system. All belts, batteries and filters have been replaced and all system functionality has been tested and reviewed.
For this commercial customer in Margate, we arrived to perform the scheduled routine maintenance on all of their YORK systems. These preventative measures are necessary to protect your HVAC investment and ensure the longevity and functionality of the system.
For this commercial customer, we arrived onsite to address an AC leaking water into the hallway of their facility. Our technician arrived and unclogged the drain line and the system was back to running without issue.
We arrived to this commercial customer's facility to address a system that was not cooling properly. After checking the system, we discovered that the ac repair needed was due to a blown transformer.
During this commercial call, the customer let us know that one of the systems is making weird noises. When we arrived on the scene, we ran a full diagnostic and survey of the entire AC system, there was no noise present at the time of inspection. We changed out the batteries and the thermostat. We advised that if this happens again, to record the timing and reach back out.
During this scheduled maintenance for a commercial customer, we changed out the belts and filters on 8 different root tap systems as well as inspected and tested all electrical components and cleaned the drain lines. After inspection of all the systems, one unit needs to be replaced instead of suggesting costly repairs.
One of this commercial customer’s rooftop system was not cooling properly. After review, the filter and blower cabinet was misplaced. Once the panel was screwed into place with new screw, the system resumed proper function.
At the residential call in Lauderdale Lakes, we found that the system was old. We tightened the mechanical fittings and the system is operating when all the system's functions were reviewed.