Everyone is very professional and works hard from the beginning to the end to ensure everything is done properly. This is a truly unique company in that they genuinely care about giving quality customer service. The prices are very reasonable but, honestly this company is still worth using even if the prices were higher. You can rest assure that the job is done correctly and that is worth more in the long run, than saving a few bucks. Thanks again for all your help!!!
Quick and detailed service by GMC tech. AC is working well now.
This commercial facility in Margate was having some trouble with making sure heat was being ventilated out of their kitchen. After some much needed AC repair their air flow issue is solved.
For this commercial customer in Margate, we arrived to treat an air conditioner not cooling. After our technician ran a full diagnostic, we discovered that there were some much needed AC repair due to not keep up on maintenance.
We installed a brand new system at this commercial facility in Margate. This new high efficiency system perfect for their facility
For this residence in Margate, we arrived to an AC not cooling. After our technician performed a full inspection of the entire system, we discovered a few things that needed to addressed including a leak of freon. Due to the severity of these repairs and the age of the system, we recommend for this customer to consider replacement over repair.
This commercial customer in Margate was suffering from their ac not cooling and in need of AC repair. After our technician ran a full diagnostic of the issue, he was able to tight all the fuse connections and get their system back up and running.
This commercial customer Margate needed some AC repair on one of their systems. After we ran a full diagnostic on the system, our technician discovered that the coils needed to be rinsed. Although this will help, the system is from 2005 and we do not recommend AC repair at this time. AC Replacement is a much better and cost effective option for this customer.
We arrived to this commercial facility to take care of some cleaning and maintenance services including the evaporator coil cleaning.
This commercial customer called for two systems that were not cooling correctly. Both were in bad shape, we found there were multiple issues including an extremely dirty drain line, drain pan and drain pump. There was low voltage and wiring issues that we were able to correct and get the Air Handler to turn on again. The condensing unit had no power due to burnt up wires. Both the contactor and dual run capacitor need to be replaced. We highly recommend against repair. These systems needs replacement and are in bad shape due to not having regular maintenance and upkeep.
For this residential replacement, we are upgrading to a YORK 2-Ton Condenser and pancake unit. With the installation of a new system, the customer receives a Service Partner Plan agreement, GMC's bi-annual maintenance check up.
Replaced liquid line drier on a carrier air conditioning package unit checked system operation left unit functioning properly
Adjusted Air Conditioning programming on the thermostat at FCC college
Preventive maintenance complete with unit checked.
Working on an American Standard residential system in margate Florida. Customer had water leak issue. Found that water leak was due to drain being clogged up. Drain was cleared and unit is now running and cooling properly.
Service system and diagnostic