For this commercial customer in Miami, we returned to perform AC repair that was discovered during our preventative maintenance visit.
For this residence in North Miami, we arrived to perform a precision tune up to make sure this system is running efficiently and to catch any needed AC repair before a potential breakdown head of the summer season.
For this commercial customer in Miami, we arrived to replace condenser fan motor and blade. When removing the old motor, we found the plate that secures the motor to the fan guard welds had failed. After repair, this system was back to running at peak performance.
We arrived to this commercial customer in Miami to a system AC not cooling. We arrived onsite to the AC's drain needing repair. The pump also needs to be replaced to get this YORK system up and running.
We arrived at this commercial facility to perform some much needed AC services and AC repairs including an evaporator coil cleaning and some duct repair.
Our technician arrived to this commercial facility in Miami Gardens to one of their suites’ AC not cooling, after a full diagnostic we performed we discovered that the batteries needed to be changed in the thermostat. The system still was not pumping the correct air flow to the suite so we checked the ducts and found that the main supply was being disrupted. Once approved, our technician performed the needed duct repair and everything as cooling normally.
We arrived to perform some much needed ac services on the system's at this commercial customer in Miami. Ac repair and ac services needed include: coil cleanings and duct work repair.
We replaced their old system with a brand new energy efficiency system. Now this customer will have better indoor air quality and efficiency.
We arrived at one of our commercial customer’s facility to help get one of their systems up and running. Once arriving on the scene, we began the ac repair. We found the system in bad shape due to lack of maintenance. We did the necessary repairs to get this system up and running. We will need to return to complete a full coil cleaning to ensure proper airflow through the unit.
This commercial customer in Miami Gardens called for ac repair on a system that was not cooling. We discovered that this system has never had regular maintenance or service. Firstly, the system is very old with a condensing unit from 2007 and a air handler from 1985. The system is in bad shape due to age including rust and damage to multiple key components. Due to the condition, our technician recommended against ac repair and offered a quote to replace instead.
Bard wall unit replacement
We returned to this commercial customer’s facility to continue the maintenance on their extensive system. After performing a precision tune up along with changing the filters and clearing the drain lines, we discovered that the only service needed was a blower wheel cleaning in room 313.
Our Production Manager went to the commercial customer's facility to inspect the installation area, take measurements, and make materials list for this upcoming installation.
We visited one of this commercial customer’s multiple facilities throughout South Florida for a system not cooling, after a full diagnosis of the problem we discovered that the condenser fan motor, blade and capacitor were faulty and needed replacement. After the new parts were installed the system has returned to cooling properly.
Performed preventative maintenance on a York AC system. During maintenance, we made sure to perform sterilization of Air handler. Once the system was sterilized, we ensured the unit was operating properly by performing a full system inspection. At this time the unit is working and cooling properly.