For this commercial facility in Miami, we performed the much needed AC repair while onsite for this preventative maintenance.
We were called out to Miami Gardens to address one of this facility's systems was not cooling properly. Our technician discovered that the AC repair needed included a fan motor and blade replacement.
We arrived in Miami to do the preventative AC maintenance created by our service manager to address the needs of their specific fleet.
In Miami, this commercial facility was due for their preventative maintenance. This air conditioning maintenance is important to insure peak performance especially on system that are used often and for long periods of time.
We arrived to this commercial facility to perform the preventative maintenance for this fleet of YORK systems. Since these systems are in constant use, it is extremely important to stay up to date on maintenance to avoid sudden breakdowns.
In Miami Gardens, this commercial facility was having some issues with their YORK system cooling. Our technician arrived to correct this breakdown and had their system up and running in no time!
For this commercial facility in Miami, we arrived to address an issue of an AC not cooling. After a full check of the system it was discovered that it was a thermostat issue. Once the thermostat was adjusted, the system was back to cooling.
For this commercial customer in Miami, we returned to perform AC repair that was discovered during our preventative maintenance visit.
For this residence in North Miami, we arrived to perform a precision tune up to make sure this system is running efficiently and to catch any needed AC repair before a potential breakdown head of the summer season.
For this commercial customer in Miami, we arrived to replace condenser fan motor and blade. When removing the old motor, we found the plate that secures the motor to the fan guard welds had failed. After repair, this system was back to running at peak performance.
We arrived to this commercial customer in Miami to a system AC not cooling. We arrived onsite to the AC's drain needing repair. The pump also needs to be replaced to get this YORK system up and running.
We arrived at this commercial facility to perform some much needed AC services and AC repairs including an evaporator coil cleaning and some duct repair.
Our technician arrived to this commercial facility in Miami Gardens to one of their suites’ AC not cooling, after a full diagnostic we performed we discovered that the batteries needed to be changed in the thermostat. The system still was not pumping the correct air flow to the suite so we checked the ducts and found that the main supply was being disrupted. Once approved, our technician performed the needed duct repair and everything as cooling normally.
We arrived to perform some much needed ac services on the system's at this commercial customer in Miami. Ac repair and ac services needed include: coil cleanings and duct work repair.
We replaced their old system with a brand new energy efficiency system. Now this customer will have better indoor air quality and efficiency.