In Palm Beach Gardens, this commercial customer was due for their maintenance. Our preventive maintenance plan is created by our service manager to address the specific needs of their fleet of Carrier systems.
We arrived to this customer in Palm Beach Gardens to a system not cooling at all. This AC was not cooling and our technician ran a full diagnostic of the system to discover the problem. After this inspection, the AC repair needed was a faulty run capacitor. Now that that has been changed out, the system is back to cooling properly.
Preventive maintenance complete with unit checked for proper.