We arrived at this commercial facility in Sunny Isles to repair a chilled water pump for their extensive HVAC system. Our technician discovered that the AC repair that needed to be performed was an electrical circuit issue. Once resolved, the system was back to cooling and running properly.
We arrived to this commercial customer who was having trouble with their ac system not working. After a full inspection of the system, we discovered that the issue was because of a faulty circuit. After replacement and a reset of the breakers this customer’s system was back to running at peak efficiency!
This commercial customer’s chiller was in need of a new evaporator barrel which exchanges heat between one refrigerant and another. The technician left with the chiller operating at peak performance.
Service carrier Air conditioning fan coil unit
Remove and clean evaporator coil and blower assembly