Efficient courteous and clean
Response from GMC Air Conditioning Services, LLC:
Mr. Shapiro, we are delighted to have you apart of the GMC team. Thank you for taking the time to leave your feedback. Thank you for your business and take you for the 5-stars!
GMC responded to my issue immediately with a knowledgeable, professional, courteous service technician.
We arrived to this commercial facility in West Palm Beach to a system that was not cooling, while onsite we found that there were some AC repairs needed to get this system up and running. Once fixed, this system was back to cooling!
In West Palm Beach, we arrived to install a brand new YORK system in a classroom. This new system has an extended warranty which ensures the cost of parts is covered in 10 years.
For this residence in West Palm Beach, we arrived to perform the preventative maintenance to help keep this customer' YORK system running at peak efficiency and to avoid sudden breakdowns.
We arrived in West Palm Beach to a customer having issues with their AC cooling at all. Our technician arrived to to address this AC breakdown and found that the system was down due to lack of AC maintenance.
Customer with water source heatpump condensation problem. Cleared drain line and adjusted pan for more positive drainage.
For this commercial facility in West Palm Beach, we arrived to finish some much needed AC repair for this Carrier system.
This commercial facility, they had who systems down that needed to be addressed. Our technician preformed a full diagnostic on both systems to figure out the issue. Once discovered, our technician preformed the much needed AC repair to get their systems back up and running.
This residential customer in West Palm Beach was having trouble with their older thermostat and Air conditioning. Our technician arrived and realize that there was going to be some extensive and costly AC repair, so our technician recommended AC repair
For this commercial customer in West Palm Beach, we arrived to a system not keeping their facility cool in the late afternoons. After our technician ran a full diagnostic of the system we discovered that the thermostat needed to be reprogrammed but there is a leak in the system. For now the system is cooling but we will need to return to address the larger issue.
We arrived to this commercial customer in West Palm Beach where their system was not bringing the room down to temperature. After running a review of the entire system, the thermostat needed to be reprogrammed. The drain line was also clogged which was causing a cooling disruption.
After a power surge over the weekend, our technician arrived to make sure the systems on site were still cooling properly. After a full inspection of the fleet, everything was fine and good to go.
We arrived to this commercial customer in West Palm Beach to complete the scheduled maintenance on their fleet of systems at this facility. Each system had their belts and filter changed, their operations checked and their drain lines and pans cleared.
For this commercial facility in West Palm Beach, our technician arrived to an AC not cooling properly. After we ran full diagnostic of the system, we discovered a wiring and electrical issue. Our technician was able to correct the problem onsite with the tools on his truck and get this system up and running again.
We arrived at this commercial facility to work on an AC making loud noise. Once our technician was onsite, he reviewed all key components and checked the electrical and safety features for proper functionality. After review, our technician This AC is supplying air to the IT room which can be very hot and needs cooling to function. There was extensive repair on this older system needed, and replacement is highly recommended. Our technician got the system running for the time being as the customer makes a decision on how to move forward.
We returned to complete the schedule maintenance for this extensive facility with a fleet of systems that need tending to.