Of course some one turned off the circuit breakers I had checked the circuits to make sure that the problem was not a tripped circuit I thought i had checked everything except seeing if the circuit breakers where in the off position seems like some one turned off the breakers I will not make that a problem again
Upon arrival found unit with a bad capacitor, replaced capacitor and checked system and found that the fan motor is bad which in turn caused the capacitor to fail. Need to replace the condenser fan motor, capacitor and clean condenser coils. Replaced condenser fan motor, dual capacitor and cleaned both condenser coils. Upstairs system is functioning properly at this time.
Found customer had heat on upstairs and cool on Downstairs. I explained operation and checked zone dampers. Unit is operating properly at this time.
Installed new unit
Checked system found a leak in the evap coil. Need to be replace. Inform customer, customer said he going to call his Home Warranty Ins.
Performed a check on the Geotherm and found no high voltage coming to unit. I found two breakers to the unit were off. Turned breakers on. Checked water flow and temperature. Unit is operating properly at this time.
Completed start up for main unit, unit is working properly at this time.
Invoice for New Units
Quote for new units
Invoice for Maintenance Agreement
Preformed gold winter maintenance on a Trane split heat pump HVAC unit (downstairs), no faults found at this time
Preformed gold winter maintenance on a Trane split heat pump HVAC unit (upstairs), no faults found at this time
Replaced blower motor drawing .7 amps, unit functioning properly at this time
Preformed platinum winter maintenance on a Carrier split heat pump, no issues at this time. Cleaned drier vent
Responded to a no a/c call on a FHP geothermal package heat pump HVAC unit, found blower motor bad. Need to replace blower motor. Waiting on Fergusion to call back with information.