Arrived to no A/C and found a bad 45/5 capacitor. Changed capacitor and checked amp draws and R22 pressures. Unit is operating properly at this time.
Install 3 Gas Packs
Install Gas Boiler
Responded to a no a/c call on a Lennox gas package HVAC unit, found the capacitor bad and needs to be replaced.
Replacement of Gas Package Unit
Checked a Lennox gas package unit and found leaking evaporator coil, have to call Tuesday and find out cost of coil.