Great service. Saving us when others could not. Will stay with Gore for a long time Thank you,
He did a great job, He was also a friendly person
The tech took extra time to go over everything! It has been sometime since this kind of service has been done to my unit. Very happy!
I was well pleased with Hans - He was very nice and answered any questions I had. He was right on time and checked things out to my expectations.
This company has always responded immediately when I have needed them. Fast and affordable service by people I know and trust.
Invoice for New Unit, Financed Through Enerbank with 10 Year Labor Warranty
Installed new unit
Found unit with a leaking evaporator coil and an improperly installed condenser fan motor and dual capacitor. Suggest replacing system due to age and condition.
Upon arrival found the unit with dirty condenser coils, cleaned condenser coils and checked operation. Found unit with a weak capacitor and low on refrigerant. Replaced capacitor and added 1.5lbs of R-22, system is functioning properly at this time.
SHMM5ZYZG5-2...received a call for no air. Upon arrival, found unit to be 22 years of age with a leaking EVAP coil. Called in report to HomeServe. Coil is not covered. Approval for call out and abortive fee.
Found unit with a severely stopped up filter in the home, removed filter and checked system. System is functioning properly. Thermostat was set to 70 on arrival, between dirty filter and conditions outside of design parameters system could not hold a 70* temperature.
Performed a Gold ESA Summer Maintenance. Checked and cleaned coils. Checked amp draws on motors and compressor. Checked thermostat, temperature split, capacitor and 410A pressures. Unit is operating properly at this time.
Arrived to no A/C call. Diagnosed a bad defrost board. Going to get board and return. Customer paid half for repair. Replaced defrost board. Checked operation. Unit is operating properly at this time.
Checked system. Everything was ok system operating fine at this time
Performed a Gold ESA Summer Maintenance. Cleaned coils. Checked amp draws on motors and compressor. Checked capacitors. Checked 410A pressures. Checked temperature split. Checked filter, thermostat. Unit is operating properly at this time.
Performed an ODS inspection on a LHP propane/LP gas logs. I cleaned burner, checked connections for gas line. There is no gas in home at this time but all components are up to code. These are unvented logs.