Upon arrival found run capacitor blown, replaced run capacitor to make sure system would function. System is now running, would suggest cleaning the condenser coils so I can accurately check the refrigerant pressures. Cleaned condenser coils and found unit low on refrigerant. Customer would like to just charge system since the state is buying her home in the next year, added 3lbs of R-22. System is functioning st this time.