Prompt, quick, respectful, professional. Couldn’t ask for more.
I arrived for a non member no heat call. I first inspected the system and found that the blower motor was overheating and leaking oil. I also found the capacitor to be completely depleted. I let the system cool off and cycled the system back on with a new capacitor. The motor came on and the system is heating normally. We did not have the proper motor brackets to mount a new motor. I told the homeowner that if the motor fails within 30 days we will replace the blower motor on the package unit and subtract the $221.85 capacitor replacement from the blower motor cost. This will also have no diagnostic cost to install this same blower motor. The homeowner signed up on a white and blue club plan. The package unit is on the white club plan but it does not have any duct on this system. The main system to the home is one we installed and we and we are going to use the free duct cleaning from the white plan to cover the duct cleaning on the split system we installed.
Black Friday furnace tune up special, customer gets a free Summer tune up with todayâ€™s furnace tune up. Spoke with customer and at this time, the summer tune up is scheduled for June 24, 2021. Asked about filters and changed customer supplied 14x24 and 16x25 filters and customer purchased a 14x14 filter from us. Asked how home has been heating and cooling and it is doing well. Went in attic and checked ductwork, flue and insulation. Attic insulation from where I can see looks to be a bit low, but home is being renovated. Ductwork is hanging a little loose , but is connected well. Checked furnace blower, blower capacitor, inducer and burners. Blower capacitor is reading low but still in range at 4.8 / 5.0 mfd. Cleaned flame sensor. Adjusted and reset loose wiring and hoses. Checked drain line and plenums. Cycled system on heat and adjusted gas pressure, it was set to 5.7 - adjusted to 3.54 w.c. Replaced gas caps. Checked amps and electrical. Measured heat rise and delta t. System is h
Remove 8 from kitchen install 8,66 wye. Run 10 inch return from master area. Run 10,8,8 wye to same area 6â€ register and boot + trip
Came out to call. Customer stated AC wasnâ€™t keeping up lately on hot days and it started to freeze up constantly. Customer thought that there could possibly be a leak. I checked system over and found the AC low on refrigerant. I discussed with customer about what I found and talked about options. Customer wanted me to go ahead and do a leak search on the system. As I was about to pump the AC down. I found a significant leak at the suction line king valve. It had a lot of pressure built up and was bubbling when I took the cap off. I went back to discussing different options with customer. Went over repair vs replace. Customer wants an estimate for both and also wants to know if the part is available tomorrow. Told customer I would check on availability.
Performed 79 non club tune up. Changed customer supplied filters. Washed condenser. Test all capacitor and motor amp draw. Test compressor amp draw. All amp draw in range. Refrigerant levels are in range. System is cooling at this time. Gave estimate to install ductwork to back addon and estimate for minisplit. Customer will think this over and call back.
I came out for a no cool and condensate leak. I checked the system over and found the system not running because the emergency pan was full, which tripped the float switch. There is a PVC tee on the drain line before the P-trap, which didnâ€™t have a cap on it. The P-trap was clogged and it overflowed out the top of the tee and onto the decking and down into the kitchen ceiling. With approval, I cut the clogged P-trap out, installed a new P-trap and shortened the drop on the drain so it has proper fall along the entire drain line. I also vacuumed out the emergency pan. I cycled the system and checked all operations. All working properly. The decking and some insulation is saturated, so there still may be some condensation dripping from the ceiling until it fully dries.
I came out for a no cool on the upstairs system. I checked the system over. I found the blower motor not operating. He had a power surge the other day and the system hasnâ€™t worked right since. The blower motor/module has failed. Iâ€™ll need to call a Carrier to get a price and availability of the motor/module and call back with a price. And a price to replace the Air Handler as well. AH M#FV4ANF003000ABAA S#:2699A1I821
Gave estimate to replace trailer system. Unable to get customer financed at this time. Customer will explore options and call back.
I arrived to inspected the refegerant charge on a system we recently installed. I had the homeowner turn the system on and let the system run. I found the subcooling to be operating at 12.8 deg and the system calls for 1p deg subcooling. The temperatures difference from supply to returning was 18.1 degrees. I did not see any reason to adjust the refegerant charge. This system is running and operating per manufacture specifications.
Came out to call. Customer said AC wasnâ€™t cooling and the heater was causing the breaker to trip. I checked system over and found that the heat strips and AC were coming on at the same time. Went through wiring to make sure nothing was wired wrong. Checked thermostat wiring as well. Once I checked wiring, I went to the components. I turned system off and heat strips were still coming on. Fan would kick on and not shut off. After running through diagnostics. I found the double stacked sequencer was passing voltage to the heat strips without it calling for it. Discussed with customer about repair. I replaced sequencer and wired it in. Checked both heat and AC to ensure system was working properly.
Preventative Maintenance Service on 21 year old Frigidaire Furnace. Blower motor is making a loud noise. Repair or replace needed
Coleman unit not working. Found bad transformer. Install new transformer. Test all operations.
AC maintenance on a 2008 Goodman system
Serviced a air conditioner and added refegerant to the system. I also added a safety switch to the system door drain clog problems.