Great work, on time, great personality! Enjoyed the visit
Isaac was a very nice polite young man! It was a pleasure having him service our unit!
Prompt, quick, respectful, professional. Couldn’t ask for more.
See white shield tune up.
29NOV2022 Jason B Arrived for fall tune up, spoke with Darrell about how the systems are doing. All good just getting our annual checkup. Replaced 20x25 filter on pack unit, cycled system into heating. Inspected blower heat strips, sequencers, Evap coil, and all electrical connections/ components. Blower 2.53a Cap 12.2/12.5 Heat strips ~20a Disconnect power to hp. Inspect capacitor, contactor, and all electrical components. Restore power and test rev valve and df timer. Cycle Heatpump in all stages. 44/44mfd 5/5 mfd cap Open ah disconnect power test fan balance and run cap. Cycle system In all stages. Verify amps and heat strips. Leave 20x30 filter with homeowner. Cycle system at thermostat. Inspect vents. Blower 2.5a No capacitor. Heat strips ~20a Both systems are working properly at this time.
Came out to call for a customer needing a system checked out in a home that belonged to his brother. His brother passed and he had no idea if the system works or not. I checked the system over and found the furnace shut off and the gas turned off. Customer confirmed that the home had propane. I turned the gas on and lit the pilot light. Tried to turn thermostat on, but it wasn’t operating properly. Discussed with customer about repair needed in order to get the system working properly. Customer approved replacement of the thermostat. I changed out the thermostat and made sure wiring was correct. Doublewide has no AC unit. Customer is aware of that and they will look into the possibility of getting a new one installed once they have everything figured out. After installation of thermostat, I turned furnace on and checked operation. Furnace cycled on and off just fine. Heat is operational.
I arrived for a silver membership summer tune up. I spoke with the homeowner and found that the systems are running to their expectations. I first cleaned all condensers and checked the systems operation and electrical readings. I found the capacitor to be weak with a dead frog on top of the capacitor. This can cause the capacitor to weaken and fail. I also found the contactor to be pitted and blackened. I made this aware to the homeowner and we decided to leave the system as it is.
CFO - 15 KW - 10 year parts warranty.
customer is moving forward with install
We arrived for a recall on a system we recently inspected. I spoke with the homeowner and found that the system they were having trouble with is working properly. I also found we had our previous technician work on both systems and replace both capacitors on both condensers. We cleaned both condensers and checked the systems refrigerant charge and electrical components. We talked about how our previous technician was not very clear on what he worked on. I apologize for the workmanship that our last technician provided and I assure you it will not happen again. We mounted both capacitors correctly and we agreed to pat what our last technician started for the warranty capacitor.
8-18-22 will p. Greeted customer asked what issues they were having. Customer stated that the up stairs unit was not running. I had no power at the outside unit. Flipped breaker on at system. System currently operating without powe
Came out to call for a system not cooling properly. Customer stated that the system wasn’t cooling properly and wasn’t blowing hard enough inside. I checked system over and found the AC unit operational, but the blower speed set too low and the blower wheel completely caked in debris. This is not allowing the blower to operate efficiently. I also found the blower capacitor to be depleted, and falling apart. Let customer know what I found and the repair and cleaning needed. Customer approved cleaning and repair after discussing pricing. Took blower assembly out and disassembled it. Cleaned all parts thoroughly and put it back together. Replaced the capacitor and reinstalled blower assembly. Wired blower motor to med high on the relay. Cycled system back on to recheck operation. System is now cooling the best it can given the age and condition of the system.
8-12-22 will. Greeted customer ask if he was having any issues with his unit. He said the fan would not spin after further investigation found that the fan motor was locked up. Replaced fan motor. Check refrigerant in system it was completely empty are 22 customer wanted me to just fill it up. I charge system 6 pounds of our 22 customer is aware that he has a leak and customer is also aware that his compressor is running high amps and may go out. Customer wants senior tech out to discuss replacement.
Ray F. 7/1/22. Arrived to non member ac tune up x2 and the customer met me at the front door. I introduced myself and asked how his air conditioners have been working. He stated they are all working good since we were out to add refrigerant to one of the systems recently. Previous work order says there is a leak at the king valve on one of the condensers. Customer states he is changing the air filters tomorrow. He showed me where the equipment was located and I proceeded to check all three evaporator coils and blower motors. Attic insulation is sufficient. Ductwork is strapped and in good condition. Blower motors, wheels and housings are clean. Evaporator coils are clean. Blower motor amps are normal and blower wheels are in balanced. Wiring in good condition. Condensate drain lines are clear. Return and supply temps good. Inspected condensers. Refrigerant levels are normal. Compressor and condenser fan motor amps are ok. Contactors, wiring and disconnect in good conditio
No cool upstairs. Found system very low on R-410A. Added 8lbs R-410A with homeowner approval. System is now operating normally. Homeowner is aware of suction line service valve leaking and cost to repair.
Arrived on 15 June for a no cool Blue Shield found that the heat pump capacitor was out replaced in warranty capacitor check charge on unit it has 16 super heat within degrees 10 sub cooling everythingâ€™s working with a manufacture specifications at this time.
See notes on blue tune up. Found system double filtered dual run cap at AC is slightly out on herm side. 56 degree heat rise in heat pump and 32 degree heat rise in emergency.
18MAR2022 Jason B Arrived for two system fall tune up. Spoke with Homeowner about systems performance. Cycled both systems on at thermostat then disconnect power at air handler/pack unit. Pull blower and coil doors,inspect heating elements sequencers and amps, capacitors and blower motors. Take delta Ts and heat rises. Changed filters. Found dual run cap at split system slightly out of specs at 41.5/45 systems are clean and working well. Found split system double filtered pulled 20x20 filter at air handler.