Hottest day of the year and my air conditioner goes out! Isaac pinpointed the electrical problem within minutes and fixed it immediately. I mentioned a possible problem with my ductwork, he went under the house, and sure enough, found a hole where all of my air was leaking! He patched the hole and we discussed a more permanent solution in the future. This is the coolest my house has been in 2 years!! Thanks Isaac!!!
Guys came to do a routine check up of my air conditioner, and found an unexpected problem. They were honest and did their best to remedy the problem without trying to sell me a bunch of stuff I didn't need.
Came out and checked under home where crossover duct had been tied in. On one side the start collar only protrudes 2â€ and the zip ties were not enough to hold it in place. Resealed duct in place in BOTH sides with duct on start collar, duct tape, zip tie and screws to ensure a solid hold that will not come loose. Checked fpm in supply vent and airflow is back to normal!
Replace supply junction and seal ductwork
Silver AC pm, summer rain storm during pm. Asked about micro power guard filters and UVV UVC lamps and customer wants to wait for a special deal or fall to have them replaced. Asked about hot and cold spots and customer said master bedroom struggles in the mornings, I showed them how the dampered louvres work to help with airflow. Washed heat pump and checked both capacitors. Checked blower and evap coil and both could use a cleaning in place, system could also use a duct cleaning. Foam front panel on return plenum had come loose, and taped it back in place with foil tape. Checked volt drop and and amps, and tested system in cooling and heating. System operating well at this time.
Blue SPP AC tune up. Asked about filters and customer has a hard time getting the necessary 18x30 and 18x20 filters. Will cut 20x20 and 20x30 to size for customer. Filters were recently replaced. Customer also having issue with conditioned air coming from base of mobile home. From previous no cool call, customer is aware that some is coming from patched return. Checked and confirmed that rest is coming from loose joints at the boot openings by the vents and the end caps. Will leave estimate to have work done to seal off ducts and clean ducts with shop vac while sealing. Wash condenser thoroughly, check dual cap. Checked blower and evap coil and drain line. Checked blower cap. Cycled system on and checked amp draws volts and refrigerant via delta t. System operating well at this time.
Perform blue shield protection plan furnace air conditioner maintenance. Changed all filters. Blower and evaporator are clean. Test all capacitors and motor amp draw. Test compressor amp draw. Washed condenser. All amp draw in range. Found unit slightly low on refrigerant with customer approval charged system with 14 oz of r22. System running as 18 subcool per charging chart. System is cooling at this time.
Arrived to no cool service call performed system evaluation. System installed by us in august 2019 unit still under warranty. Found liquid line weld at evaporator did not hold and had micro leak. Oil spots around weld and unit out of refrigerant. Welded all connections to evaporator coil. Tested with nitrogen for 10 min. Evacuated system and charged unit with 9 lbs r410 unit running at 11 subcool per carrier specifications. System cooling at this time. No charge to customer.
Performed a tuneup on the carrier gas furnace
Maintenance Service on Carrier Heat Pump System
AC isn’t cooling. AC Compressor isn’t working. Contactor failure and wire short. Ductwork needs to also be replaced under home
Replace under warranty control board to 2013 rheem furnace
Cleaned a drain line on a air conditioner in the attic.
AC maintenance on 2014 Carrier system
Summer air conditioning preventative maintenance. Damaged compressor repair.
Repair compressor to carrier air conditioner
AC Maintenance Service on Payne HVAC Unit