Very knowledgeable. Answered all my questions. Polite. As a retired business owner I would hire Caleb. Make sure you send him back for my next service
Tech preformed CMA INSPECTION on 6 split systems and 2 mini split systems. Tech was unable to gain access to rooftop to preform inspection on gas pack unit due to faulty door. Hotel maintenance is aware. Tech left filters for hotel maintenance. Tech found dual run capacitor weak on system 3. Capacitor rated at 45/5 mfd, tested at 7.73/ 4.24 mfd. Approved to replace by Victoria Gallagher. Tech did find condenser units 1,2 and 3 extremely dirty and clogged with lint from dryer exhaust vent. This units is limiting the airflow over the coils causing high amps on the systems. Tech recommends cleaning condenser coils. Tech has attached estimates to invoice for coil cleanings. Tech also will have comfort specialist contact customer about receiving 2 full services a year. Systems 4,5 and 6 are operating correctly at this time. Mini splits are operating correctly at this time.
was filter. not able to get to unit because there is a lot of stuff in front of it and plus they are about to have a meeting not time to move stuff maintenance say they will wash this filter
Inspection on 6 Tempstar heat pumps, 1 Reznor gas package unit, 2 Mitsubishi mini splits, washed filters, changed filters.
Changed filters, washed 9 filters.
Tech performed service on 2 Trane split systems.