George did a great job. As he always does.
PTU Heat pump
PTU Air handler
Nordyne tune up
Trane heatpump defrost coil and check freon R22
No air. Heat pump. Need to return to further diagnose system due to heavy rain.
Confirmed cracked heat exchanger in goodman furnace
Amana cleaning and service
Installed Amana heat pump
Removed outdoor section of Amana heat pump
Bryant heatpump tune up