George did a great job. As he always does.
No air call non club member
Replaced low voltage fuse in Bryant air handler
Checked over york air conditioning system
Tune up on AC
Trane heatpump replace condensate pump
Leaking water heater
Precision tune up goodman heat pump
PTU Heat pump
PTU Air handler
Nordyne tune up
Trane heatpump defrost coil and check freon R22
No air. Heat pump. Need to return to further diagnose system due to heavy rain.
Confirmed cracked heat exchanger in goodman furnace