I would recommend your company to others
Found the type of business I have been looking for. No need to look further.
We checked motor for the attic fan. Found attic fan motor seized. Furnished, wired, and replaced said attic fan. Temperature has been set on 95.
Furnished, wired, and installed 2 switches and switchlegs for Undercabinet lights in the kitchen. Wired and installed customer provided Undercabinet lights in said kitchen. Performed panel maintenance and tightened all connections. We had to cut Sheetrock. We do not patch any Sheetrock that we cut.
Replaced pressure reducing valve. Set pressure to 60 psi. Tested for leaks and non found. Replaced expansion tank. Pumped up to 60 psi. Tested and no leaks. Replaced the gas to both furnaces so that black iron comes out of the furnace per code. Cleared master bath left side sink. Found hair in the drain. Drains good with no gurgling.
install 1 inch prv on the main to lower psi below 80
install new 50 gal water heater up to code with a new thermal expansion tank and cut off with removal of the old unit 6 year rheem
Installed gas line with two cut offs for a gas grill Line is installed with 1/2 type l copper
We troubleshot and fixed reversed polarity issue on the outlets in the basement. We troubleshot and fixed non gfi protected outlets at the front and back of home. We furnished, wired, and installed a gfi in the garage to replace exposed wiring. We performed panel maintenance and tightened all connections. We furnished, wired, and replaced a total of 3 breakers that were installed improperly. During panel maintenance, we found bundled up neutrals which is against code. We furnished, wired, and installed an additional neutral bar and separated said neutrals.
Walked job with customer to give a price.
Customer has a house standing pressure of 105PSI from PRV (Pressure Regulating Valve). Replaced the single port 3/4" PRV with a new 3/4" duel port PRV. Replaced the T&P valve on the 50 gallon gas water heater. There is a one year warranty on both items. All tested great with no leaks. Pressure is now at 60PSI.
install #6 bare copper to a ground rod to properly bond the panel
moved a gas line back in the wall so that customer could put the new stove flush to the wall also the company that installed the stove to start with. had 2 gas leaks on the line
we rebuilt back bathroom commode we rebuilt the back master bathroom commode that we recommend customer change out to ensure that he doesn't have future problems we rebuilt master bathroom faucets we installed a new commode in the hall powder room bath we also snaked the office bathroom commode
rebuilt on the down stairs commode
the water heater was not leaking it was the female connection on the hot side The connection was not tight. we cut it out and replaced it
installed two sink faucets and trim one shower.