Called on a tankless water heater issue. They arrived within an hour and found the problem. Even though they were unable to get parts, they were able to assist in how to get the parts and what would need to be done to replace them.
Performed Annual Generator Maintenance in accordance with Generac recommendations. Checked/Inspected the Automatic Transfer Switch. Updated system cpu. Cleaned machine. Generator is performing well consistent with the age of unit. Ready for another year!
Install Supply Duct
Preparing home for winter vacation
Duct cleaning being done.
Full fall generator tune up
Quote on Electrical Work
Tankless control board failure
Oil change out on 16 Kw Generac