Mike was very informative and polite. Explained the service being performed
Tech was very knowledgeable and polite. Performed the work and even offered tips to improve equipment performance.
Performed Annual Generator Maintenance in accordance with Generac recommendations. Checked/ Inspected the Automatic Transfer Switch. Updated generator CPU. Thoroughly cleaned/detailed machine.
Repaired stripped Allen lugs on generator.
Replaced outlet in laundry room.
Reinstalled a 20KW Whole House Generac Generator due to unsafe & faulty wiring job by another contractor.
Performed Annual Generator maintenance. Checked/Inspected ATS. Generator is performing well.
Preseason maintenance on Bryant equipment
Weil MacLaine boiler pilot issue
Warranty gas valve replacement on AO Smith water heater
Boiler clean and check on Weil McLain system
install sump pit and sump pump
Furnace maintenance on 986TB Bryant Furnace
Converting natural gas fire place to propane.
Generator maintenance on 9kw Generac Home Standby Generator
Geothermal blower replacement
finishing up duct work