Service was fine. Glad he told me about comfort club for future maintenance of generator
Professional and knowledgeable.
Service man explained everything he was going to do and when he was done let me know what he found and everything he did
Fast, friendly service.
Friendly, knowledgeable serviceman. Helpful with suggestions for unusual situation, & cooperative with placement of outlets, etc.
The guys were so helpful and very professional n got my AC back up and running in a timely fashion!!!!
The service was performed to meet a specified timeframe on a contractual obligation. The work was performed by excellent technicians , leaving the areas clean & up to required standards.
A/C Clean&Check. 3 year old Bryant Condenser
Inspected QO service panel and stove/microwave outlet. Replaced 20amp circuit breaker.
Performed Annual Generator Maintenance in accordance with Generac recommendations. Checked/ Inspected the Automatic Transfer Switch. Updated generator CPU. Thoroughly cleaned/detailed machine. Generator is performing well.
Performed Annual Generator Maintenance in accordance with Generac recommendations. Checked/ Inspected the Automatic Transfer Switch. Updated generator CPU. Thoroughly cleaned/detailed machine.
New garbage disposal
Performed Annual Generator Maintenance according to Generac recommendations. Checked/Inspected ATS. Generator is performing well.
Install new window AC
A/C Clean&Check, 16 year old Lennox condenser
A/C Service. Found faulty thermostat
Remove and move outlets for future foundation work to be done.
New 50 gallon water heater.
A/C Clean&Check. 24 year old Tempstar condenser
Replace gas line to stove