prompt , knowledgeable
CURTIS 10-1030A 443-623-7884 cell Kitchen Suppression Inspection Semi-Annual Kitchen Inspection Equip Desc: Inspect (4) 6 Gal. Ansul Systems Inoperable Deficiency for Ansul R102 Wells 6 gallon: Same deficiency’s remain: concession stand 1,2,3,4(all systems are the exact same) ansul 6gal WELLS ventless hood (1.5galx4) -appliances need to be interlocked to system, when hood is off appliance should not be able to turn on -no electric shutdown to fryer or grill -no alarm bell -paper filters need replaced and metal ones need cleaned due to heavy grease build up ***liability disclaimer form added*** concession stand 4 -thermal detectors must have short in wiring, when interlocked is plugged in system trips, as of now only way to activate system in the event of fire in with the remote pull -filters also need changed on it, filter and service light are on
03/03 CHEF JOHNATHAN 10-1030A Kitchen Suppression Inspection Ansul R-102 3-gallon: Semi-Annual Kitchen Inspection Equip. Desc.: ANSUL 3-gallon and (1) Ansul 6 Gallon Deficiency for Ansul R102 66gallon Front hood: Salamander was added to equipment line-up and needs protection. **Repipe drops for proper coverage** System has 19 flows already
Onsite to troubleshoot inoperable horn strobe on 2nd floor. Traced circuit out to find wires disconnected in junction box above ceiling grid above FACP. Secured circuit with proper wire nut and successfully activated horn strobe on 2nd floor. Panel remained in trouble for zone 1. Found zone 1 end of line device without resistor. Placed 4.7 k resistor on smoke detector by rear of retail space and trouble cleared. System is in normal condition at the time of departure.
Portable Extinguishers and Emergency / Exit Lights Inspection
Portable Extinguishers Inspection