prompt , knowledgeable
Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 4.5 GAL & (2) EXT Alarm Int: No
Emergency / Exit Lights Inspection
Portable Extinguishers and Emergency / Exit Lights Inspection
1-5lb 6 yr Kitchen Suppression and Portable Extinguishers Inspection Ansul R-102 6-gallon Prep area: Semi-Annual Kitchen Inspection Equip Desc: (1) Ansul 6 Gallon System Annual Inspection Extinguisher Equip Desc: Inspect (2) Exts Inoperable Deficiency for Ansul R-102 6-gallon Prep area: Detection line failed due to excessive grease buildup under hood Parts needed to complete repair: **7 Ansul detectors **20ft conduit **15ft cables **2.5 labor hours Inoperable Deficiency for Ansul R-102 6-gallon Prep area: Scissor clips in duct area has excessive grease buildup and needs replacement Both 2w duct nozzles area clogged and needs replacement Inoperable Deficiency for 6L K Class Kitchen: K-guard extinguisher located in the kitchen is past due for hydro testing MFD 2014 Deficiency: Number of Extinguishers Left at Job: 1
Kitchen Suppression Emergency Service Call We need to have someone come out and service the Ansul system due to a fire in the oven last night. the Fire Marshall is requiring the system be checked before we can resume any cooking.
09/09 Tom 11-1130a Kitchen Suppression Inspection Ansul R-102 3-gallon Left side of hood: Semi-Annual Kitchen Inspection Equip. Desc.: ANSUL 3-gallon and (1) Ansul 6 Gallon Inoperable Deficiency for Ansul R102 6G Front hood: Same deficiency’s remain from last inspection: Salamander was added to equipment line-up and needs protection. **Repipe drops for proper coverage** System has 17 flows already