Joe and Travon were very knowledgeable and it was a pleasure working with them.
very nice gent great follow thru.
I can't express my gratitude enough to Paul for his assistance Wednesday. This should have been a simple test of newly installed equipment (By BFPE) but turned into a discovery of major deficiencies which made the test take much longer than anticipated. Paul's experience and attention to detail were greatly appreciated.
They did not show up for our appointment after I confirmed via email. They did not reply to my follow-up email to set up a new date, but showed up by surprise two weeks later.
Techs were professional and explained to me what they did and tested.
Technicians were prepared and did an excellent job.
dwayne 9am 240-535-6435 take hydro pump & adapter other parts on will call beltsville 9670658 Sprinkler Inspection FDC hydrostatic test for the (3) FDCs. This will require at least 8 HRS (2) TECHS and the following material- Hydro pump (1) 2.5" x 2" brass male adapters (3) 2" x 1" RCs (3) 1 x 1/2 bushings (9) 1/2" x 0-3 nipples (6) 1/2" ball valves (3) 1/2" Tees (3) 1/2 x 1/4 bushings (3) water gauges NOTE: Test will be performed on 3 separate FDC's Deficiency: **Sprinkler** 1. Need to install the following signs: (1) control valve sign for OS&Y on wet system in sprinkler room (1) control valve sign on incoming OS&Y in sprinkler room (3) aux drain signs for air drains on dry valves (1) air line sign in sprinkler valve room (1) main drain sign on boiler drain for wet system in sprinkler room (1) aux drain sign in parking space 181 on level C 2. Need to replace the following gauges: (3) water gauges in sprinkler room (2) air gauges in sprinkler room (1) water gauge in stair B,
Portable Extinguishers Inspection