Paul was very polite and knowledgeable and was more than willing to share his knowledge with myself and the utility associate!
Portable Extinguishers Repair
malve 9-10p malve meeting you 443-616-9682 no cooking install (1) K class ($275), and (2) 5 lb. ABC. Kitchen Suppression and Portable Extinguishers Inspection Semi-Annual Kitchen Inspection Equip Desc: (1) Ansul 9 Gallon System Install (1) K-Class and (2) 5lb ABC extinguishers. Create location form. Inoperable Deficiency: Ansul 9 gallon Improper coverage above (Spinning Grillers) 32inx35&3/4in #1 Stock range 18inx18in #2 Stock range 18inx18in 3) 1F nozzles protecting 6 burner range are clogged and needs replacement** (1f nozzles were replaced 2/8/2021 with swivel adapters) Fryer 24inx14in **2) 230 nozzles are clogged and needs replacement** #1 Wok 13&1/2in #2 Wok 13&1/2in #1 circular flat top range 30in (currently has 290 nozzle as protection.) *Clogged* #2 circular flat top range 30in (1n nozzle protecting appliance) *Swivel adapter needed (Swivel adapter added 2/8/2021) Flat top grill 24inx36in (1n nozzle needs swivel adapter to properly aim nozzle to appliance.) swivel ada
Annual Inspection Dept: EXTING Equip Desc: (9) EXTINGUISHERS Portable Extinguishers Inspection
tom 1230 see tom cell 410-404-1591 meeting you Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) RANGEGUARD 4 GAL Alarm Int: No Inoperable Deficiency for RangeGuard Unknown 4 Gallon Back wall by dish washer: Same deficiency’s remain from last inspection: Range Guard 4 Gallon 4 gallon cylinder is due for hydro testing MFD ( 8 burner range, 2 burner/ flat top griddle, Grill and fryer lacks detection and protection. System lacks gas shut-off gas valve frozen with heavy grease. No local bell interlock. **UL-300 upgrade needed** Deficiency for 5 ABC End of bar: 5lb abc extinguisher located at the end of the bar is due for hydro testing. Last 6 year maintenance was performed in 2013.