Dwayne was very professional and knowledgeable.
Kitchen fire suppression system inspection
Portable Extinguishers Inspection
Kitchen Suppression Inspection
02/03 Melanie 7am Kitchen Suppression Inspection Ansul R-102 6-gallon Kitchen: Semi-Annual Kitchen Inspection Equip. Desc.: ANSUL 6-gallon Inoperable Deficiency for Ansul R-102 6-gallon Kitchen: Ansul 6 gallon Detection line failed to activate due to excessive grease buildup under hood Inoperable Deficiency for Ansul R-102 6-gallon Kitchen: Ansul 6 gallon Clogged 1n nozzle above chain broiler needs replacement Replaced 2/4/2021